CHAPTER 2 DYNAMIC STABILITY MODEL OF THE POWER SYSTEM


 Rafe Haynes
 1 years ago
 Views:
Transcription
1 20 CHAPTER 2 DYNAMIC STABILITY MODEL OF THE POWER SYSTEM 2. GENERAL Dynamic stability of a power system is concerned with the dynamic behavior of the system under small perturbations around an operating condition and more specifically it is a phenomena of slow and poorly damped or sustained or even diverging power oscillations which are essentially due to varying system loads and ill controlled controllers of the system. Computer analysis of this problem requires mathematical models which simulate as accurately as the behavior of physical system but at the same time not very complex to handle. This chapter presents the development of the mathematical model for the dynamic stability analysis of Single Machine Infinite Bus System (SMIB) and Multi machine power system. 2.2 SIMPLIFIED LINEAR MODEL FOR SMIB SYSTEM In stability analysis, the mathematical model is used for dynamic analysis of power systems Assumptions The following assumptions are made for the development of simplified linear model of SMIB system:
2 2. Damper windings both in the d and q axes are neglected. 2. Armature resistance of the machine is neglected. 3. Excitation system is represented by a single time constant. 4. Balanced conditions are assumed and saturation effects are neglected Classical Machine Model In the classical methods of analysis, the simplified model or classical model of the generator is used (Kundur 994). Here, the machine is modeled by an equivalent voltage source behind impedance connected to an infinitebus as shown in Figure 2.. Infinite Bus An infinite bus is a source of invariable frequency and voltage (both in magnitude and angle). A major bus of a power system of very large capacity compared to the rating of the machine under consideration is approximately an infinite bus. x e Figure 2. Oneline diagram of SMIB The state space classical machine model is shown in Figure 2.2.
3 22 K s Figure 2.2 Classical Machine Model The state equations of the classical model are given in equation (2.): p( ω ) = Tm K S D 2H δ ω p( δ ) = ω ω (2.) 0 State vector T x = ( ω δ ) (2.2) And when the effect of flux linkage is included, three states are used to model the generator: ω, δ and E q '. The state equations are given in equation (2.3) as follows: T K K D p ω=  δ E  ω τ τ τ τ m 2 ' q j j j j p( δ ) = ω ω 0  K p E = E + E  δ (2.3) ' ' 4 q ' q ' FD ' Kτ 3 do τdo τdo where τ j = 2H, H is the inertia constant.
4 23 State Vector of the SMIB system including the effect of flux linkage is given by equation (2.4) t x [ E' q] = ω δ (2.4) where the variables are E q ' ω δ  quadrature axis component of voltage behind transient reactance  angular velocity of rotor  rotor angle in radians K to K 6 is the Heffron Philips constants (Padiyar 2002). 2.3 EXCITATION SYSTEM REPRESENTATION The excitation system model considered is the simplified form of STA model shown in Figure 2.3. A high exciter gain, without derivative feedback, is used. By inspection of Figure 2.3, the state space equations can be written as, V V t KA + st A E FD Figure 2.3 Excitation System Representation p E FD = /T A (K A V t + E FD ) (2.5) with T R is neglected, V ref =constant. And V t = K 5 δ + K 6 E q '
5 24 where E FD  Equivalent stator emf proportional to field voltage K A  Gain of the Exciter T A  Time constant of the exciter T R V t  Terminal Voltage Transuder Time Constant  Terminal voltage of the Synchronous machine V ref  Reference voltage of the Synchronous machine Combining the Equations (2.3) with the exciter equation (2.5), the complete state space description of SMIB system including exciter is given in equation (2.6). T K K D p ω=  δ E  ω τ τ τ τ m 2 ' q j j j j p δ = ω0 ω  K p E = E + E  δ ' ' 4 q ' q ' FD ' Kτ 3 do τdo τdo pe FD = /T A (K A K 5 δ + K A K 6 E q ' + E FD ) (2.6) The state vector is thus defined by Equation (2.7): t x [ E' q E FD] = ω δ (2.7) 2.4 SMIB SYSTEM REPRESENTATION WITH CPSS The block diagram of the CPSS is shown in Figure 2.4. The state equations for the same can be written as follows. p V 2 = K PSS p ω (/T w ) V 2 (2.8) p V s = (T /T 2 ) p V 2 + (/T 2 ) V 2 (/T 2 ) V s (2.9)
6 25 where K PSS  CPSS gain T, T 2  Phase compensator time constants T w  Wash out time constant CPSS V t V s Figure 2.4 CPSS Representation State vector of the synchronous machine model including PSS is given by equation (2.0): T x = [ E q' EFD V2 V s] ω δ (2.0) The block diagram of simplified linear model of a synchronous machine connected to an infinite bus with exciter and PSS is shown in Figure 2.5. V t Conventional Power System Stabilizer Figure 2.5 State Space Model of SMIB system representation with CPSS
7 DYNAMIC STABILITY MODEL OF MULTI MACHINE POWER SYSTEM In stability analysis of a multimachine system, modelling of all the machines in a more detailed manner is exceedingly complex in view of the large number of synchronous machines to be simulated. Therefore simplifying assumptions and approximations are usually made in modelling the system. In this thesis two axis model is used for all machines in the sample system taken for investigation Assumptions Made In this work the synchronous machine is modeled using the twoaxis model (Anderson and Fouad 2003). In the twoaxis model the transient effects are accounted for, while the sub transient effects are neglected. The transient effects are dominated by the rotor circuits, which are the field circuit in daxis and an equivalent circuit in the qaxis formed by the solid rotor. The amortisseur winding effects are neglected. An additional assumption made in this model is that in stator voltage equations the terms pλ d and pλ q are negligible compared to the speed voltage terms and that ω ω =p.u. The R block diagram representation of the synchronous machine in twoaxis model is shown in Figure 2.6.
8 Figure 2.6 Block diagram representation of two axis model for synchronous machine 27
9 Synchronous Machine Representation Using the block diagram reduction technique and with the simplifying assumptions the state equations for the twoaxis model in p.u. form pe d ' = {E d '  (x q x q ') I q } / τ qo ' pe q ' = {E FD  E q '  ( x d  x d ' ) I d } / τ do ' pω = {T m  Dω  T e } / τ j pδ = ω  (2.) where the state variables are E d '  direct axis component of voltage behind transient reactance E q '  quadrature axis component of voltage behind transient reactance ω  angular velocity of rotor δ  rotor angle in radians and T e = E d 'I d + E q 'I q (x q ' x d ' ) I d I q τ j = 4πfH x d  direct axis synchronous reactance x q  quadrature axis synchronous reactance x d '  direct axis transient reactance x q '  quadrature axis transient reactance τ do '  direct axis open circuit time constant
10 29 τ qo '  quadrature axis open circuit time constant T e  electrical torque of synchronous machine T m  mechanical torque of synchronous machine D  damping coefficient of synchronous machine E FD  Equivalent stator emf corresponding to field voltage I q  quadrature axis armature current I d  direct axis armature current H  inertia constant of synchronous machine in sec f  frequency in Hz A multimachine power system is shown in Figure 2.7 and the network has n machines and r loads. The active source nodal voltages in Figure 2.7 are taken as the terminal voltages V i, i =.2.n instead of the internal EMF`s. The loads are represented by constant impedances and the network has n active sources representing the synchronous machines. Figure 2.7 Multimachine with constant impedance loads
11 30 This network is reduced to a nnode network shown in Figure 2.8 in which the current and voltage phases of each node are expressed in terms of the respective machine reference frame. Figure 2.8 Reduced nport network The objective here is to derive relations between v di and v qi, i=,2,.n, and the state variables. This will be obtained in the form of a relation between these voltages, the machine currents i qi and i di, and the angles δ i, i=,2,.n. For convenience we will use a complex notation as follows. For a machine i we define the phasors V and I i i as V = V + jv ; I = I + ji (2.2) i qi di i qi di
12 3 where V = v / 3 : V = v / 3 qi qi di di I = i / 3 : I = i / 3 qi qi di di and where the axis q i is taken as the phasor reference in each case. Then we define the complex vectors V and I by V V + jv q V V jv 2 + V = = V V + jv qn n d q 2 d 2 dn (2.3) I I I + ji q d I I + ji 2 q 2 d 2 = = I I + ji qn dn n (2.4) The voltage Vi and thecurrent I i are referred to the q and d axes of machine i. In the other words the different voltages and currents are expressed in terms of different reference. To obtain general network relationships, it is desirable to express the various branch quantities to the same reference which is given by equation (2.5): The node voltages and currents are expressed as Vˆ and ˆI i i, i =,2,..n, and ˆI = YV ˆ (2.5) where Y is the short circuit admittance of the network.
13 Converting to Common Reference Frame Let us assume that we want to convert the phasor Vi V jv qi di = + to the common reference frame (moving at synchronous speed). Let the same voltage, expressed in new notation, be ˆV = V + jv i Qi Di as shown in Figure 2.9. where, = + and ˆV = V + jv i Qi Di (2.6) Vi V jv qi di D ref V Di V i = V ˆi d i q i V qi V di δ i δ i Q ref V Qi Figure 2.9 Two frames of reference for phasor quantities From the Figure 2.9 V Qi = [Vqi cos δ i Vdi cos δ i ] (2.7) V = [V cos δ V cos δ ] Di di i qi i (2.8) V + V = (V cos δ V cos δ ) + (V sin δ + V cos δ ) Qi Di qi i di i qi i di i (2.9) ˆV i j i = V e δ i (2.20)
14 33 The equation (2.20) can be written in generalized matrix form as below jδ V jv e V jv Q D + q d jδ2 V + jv e 0 V jv Q2 D2 + = q2 d V jv + V qn jv Qn Dn j n + δ e dn (2.2) jδ e 0 0 jδ2 e 0 T = 0 0 jδn e (2.22) The equation (2.20) can be written as ˆV = TV (2.23) Thus T is a transformation that transforms the d and q quantities of all machines to the system frame, which a common frame is moving at synchronous speed. The transformation matrix T contains elements only at the leading diagonal and hence we can show that T is orthogonal, i.e. T  = T *. Now the equation (2.23) can be rewritten as * ˆ V=T V (2.24) Similarly for node current Î = TI (2.25)
15 34 * ˆ I = T I (2.26) we get Substituting equation (2.25) and equation (2.23) in equation (2.5), I = MV (2.27) where M = T  YT (2.28) Linearizing equation (2.27) and making necessary substitutions (Anderson and Fouad 2003), the following equations are obtained. I qi = G ii V qi B ii V di + n [ Y ii cos(θ ij  δ ij0 ) V qj ] j=  n [ j= Y ij sin (θ ij  δ ij0 ) V dj ] + n [ Y ij {sin(θ ij  δ ij0 ) V qj0 + cos(θ ij  δ ij0 )V dj0 ] δ ij j= ; i =,...n (2.29) I di = B ii V qi + G ii V di + n [ Y ij cos (θ ij  δ ij0 ) V dj ] j= + n [ j= Y ij sin (θ ij  δ ij0 ) V qj ] + n [ Y ij {sin (θ ij  δ ij0 )V dj0  cos(θ ij  δ ij0 )V qj0 ] δ ij j= ; i =,...n (2.30) The state space model for linearized system is obtained by linearizing the differential and algebraic equations at an operating point. While doing this linearization process, additional terms involving terminal voltage components (which are not state variables) remain in the differential
16 35 equations. To express the voltage components in terms of state variables, the machine currents are also linearized and expressed in terms of state variables and voltage components. Finally the current components are eliminated using the interconnecting network algebraic equations. From the initial conditions, E d ' i0, E q ' i0, I qi0, I di0, E FDi0 and δ i0 are determined. Linearizing equation (2.) we get p E d ' i = { E d ' i  (x qi  x q ' i ) I qi } / τ qo ' i ; i =,...n p E q ' i = { E FDi  E q ' i + ( x di  x d ' i ) I di } / τ do ' i ; i =,...n p ω i = { T mi (I di0 E d ' i + I qi0 E q ' i + E d ' i0 I di +E q ' i0 I qi ) D i ω i } / τ j ; i =,...n (replacing V by E'): p δ i = ω i ; i =, n (2.3) Substituting equations (2.29) and (2.30) in equation (2.3). p E d i = {[(x qi  x q ' i ) B ii ] E d ' i τ qo ' i + (x qi  x q ' i ) n [ Y ik {sin (θ ik  δ ik0 ) E d ' k (x qi  x q ' i ) G ii E q ' i k=  (x qi  x q ' i ) n [ Y ik cos (θ ik  δ ik0 ) ] E q ' k k=  (x qi  x q ' i ) n [ Y ik cos(θ ik δ ik0 )] E d ' k0 +Y ik sin ((θ ik  δ ik0 ) E d ' k0 ] δ ik } k= i =,2.n (2.32)
17 36 p E q ' i = τ ' do i {[(x di x d ' i ) B ii ] E q ' i + (x di x d i ) n [ Y ik {sin (θ ik  δ ik0 )] E d ' k + (x di x d ' i ) G ii E d ' i k= + (x di x d ' i ) n [ Y ik sin (θ ik  δ ik0 ) ] E q ' k k=  (x di x d ' i ) n [ Y ik cos(θ ik δ ik0 ) E q ' k0 Y ik sin((θ ik δ ik0 )E d ' k0 ] δ ik + E FDi )} k= i =,2.n (2.33) p ω i = τ ji {[ T mi  D i ω i [I di0 + G ii E d ' i0  B ii E q ' i0 ] E d ' i  [ I qi0 + B ii E d ' i0 + G ii E q ' i0 ] E q 'i  n [ k= Y ik cos (θ ik  δ ik0 ) E d ' i0  Y ik sin (θ ik  δ ik0 ) E q ' i0 ] E d ' k  n [ k= Y ik sin (θ ik  δ ik0 ) E d ' i0 + Y ik cos (θ ik  δ ik0 ) E q ' i0 ] E q ' k  n [ k= Y ik cos (θ ik  δ ik0 ) (E q ' k0 E d ' i0 +E d ' k0 E q ' i0 ) + Y ik sin ((θ ik  δ ik0 ) (E d ' k0 E d ' i0 +E q ' k0 E q ' i0 ) δ ik } i =,2.n (2.34) p δ i = ω  ω i (2.35) i = 2,3.n taking machine as reference.
18 37 The above set of equations (2.32 to 2.35) gives the state space model of nmachine system. 2.6 EXCITER REPRESENTATION The state space equation of the exciter can be derived from the block diagram of the exciter shown in the Figure 2.3. From the Figure 2.3, we get K A EFD = + STA V t (2.36) For n, number of exciters, the state equations is as follows: K p E =  V + V  E ; ( ) Ai fdi Refi i fdi TAi TAi i=, n (2.37) Now the state vector of the n machine state model including exciter equation is as follows. X T i = [ E d ' i E q ' i ω i δ i E FD i ] ; i=, n (2.38) 2.7 CONVENTIONAL POWER SYSTEM STABILIZER REPRESENTATION The Conventional Power System Stabilizer (PSS) adds damping to the generator rotor oscillations by controlling its excitation using auxiliary stabilizing signals. To provide damping, the stabilizer must produce a component of electrical torque in phase with the rotor speed deviations.
19 38 The important blocks in a power system stabilizer are: Washout circuit. Phase compensator. Stabilizer gain. The state space equation for the power system stabilizer (PSS) can be obtained from the block diagram shown in Figure 2.0. Figure 2.0 Conventional Power System Stabilizer Structure (CPSS) From the wash out block, we get st V = (K ω) w 2 PSS + stw (2.39) p V 2i = K PSSi p ωi (/T wi ) V 2i ; i =,...n (2.40) From the phase compensator block we get + st V V + st 2 = s 2 (2.4) From equation (2.4) we get p V si = (T i /T 2i ) p V 2i +(/T 2i ) V 2i (/T 2i ) V si ; i =,...n (2.42)
20 39 The state vector of the complete system after the inclusion of power system stabilizer is as follows: x T i = [ E' di E' qi ω i δ i E FDi V 2i Vs i ] ; i=, n (2.43) 2.8 FUZZY LOGIC BASED POWER SYSTEM STABILIZER (FPSS) FPSS. Figure 2. shows the schematic block diagram of the system with d dt ω ω FPSS V s + V t  + V ref Power System Generator and Exciter ω Figure 2. Structure of the Power system with FPSS Speed Deviation of the synchronous machine ( ω) and its deviation ( ω ) are chosen as inputs to the FPSS. Simulation of the sample SMIB system without PSS is carried out for several operating conditions and different disturbances and the inputs are normalized using their estimated peak values. Seven labels are taken for both the inputs and output. The labels are LP (large positive), MP (medium positive), SP (small positive), VS (very small), SN (small negative), MN (medium negative) and LN (Large negative). Linear triangular membership function is used in the design of FPSS. In our design of FPSS, the fuzzy sets with triangular membership function for ω are shown in Figure 2.2. The membership function for similar to the above Figure 2.2. ω and Vs are
21 40 LN MN SN VS SP MP LP Figure 2.2 Triangular membership function of ω Khan 2000). Table 2. shows the rules of fuzzy logic based PSS (Lakshmi and Table 2. Rule Table of fuzzy logic PSS ω LP MP SP VS SN MN LN LP LP LP LP LP MP SP VS ω MP LP LP MP MP SP VS SN SP LP MP SP SP VS SN MN VS MP MP SP VS SN MN N SN MP SP VS SN SN MN LN MN SP VS SN MN MN LN LN LN VS SN MN LN LN LN LN
22 4 2.9 CONCLUSION Mathematical model of SMIB system for dynamic stability analysis is presented in this chapter. Various state variables with PSS, system matrix including static exciter and CPSS are included in this chapter. Block diagram of simplified linear model of SMIB including exciter and CPSS is also neatly presented in this chapter. Non linear mathematical model representing the dynamics of the multi machine power system combining the synchronous machine model, excitation system (IEEE Type ST A), with conventional power system stabilizers are described in this chapter. The fuzzy logic based PSS model is also described.
From now, we ignore the superbar  with variables in per unit. ψ ψ. l ad ad ad ψ. ψ ψ ψ
From now, we ignore the superbar  with variables in per unit. ψ 0 L0 i0 ψ L + L L L i d l ad ad ad d ψ F Lad LF MR if = ψ D Lad MR LD id ψ q Ll + Laq L aq i q ψ Q Laq LQ iq 41 Equivalent Circuits for
More informationEE 742 Chapter 3: Power System in the Steady State. Y. Baghzouz
EE 742 Chapter 3: Power System in the Steady State Y. Baghzouz Transmission Line Model Distributed Parameter Model: Terminal Voltage/Current Relations: Characteristic impedance: Propagation constant: π
More informationLesson 17: Synchronous Machines
Lesson 17: Synchronous Machines ET 332b Ac Motors, Generators and Power Systems Lesson 17_et332b.pptx 1 Learning Objectives After this presentation you will be able to: Explain how synchronous machines
More informationJRE SCHOOL OF Engineering
JRE SCHOOL OF Engineering Class Test1 Examinations September 2014 Subject Name Electromechanical Energy ConversionII Subject Code EEE 501 Roll No. of Student Max Marks 30 Marks Max Duration 1 hour Date
More informationPower System Stability and Control. Dr. B. Kalyan Kumar, Department of Electrical Engineering, Indian Institute of Technology Madras, Chennai, India
Power System Stability and Control Dr. B. Kalyan Kumar, Department of Electrical Engineering, Indian Institute of Technology Madras, Chennai, India Contents Chapter 1 Introduction to Power System Stability
More informationSymmetrical Components Fall 2007
0.1 Variables STEADYSTATE ANALYSIS OF SALIENTPOLESYNCHRONOUS GENERATORS This paper is intended to provide a procedure for calculating the internal voltage of a salientpole synchronous generator given
More informationTransient Stability Analysis with PowerWorld Simulator
Transient Stability Analysis with PowerWorld Simulator T1: Transient Stability Overview, Models and Relationships 2001 South First Street Champaign, Illinois 61820 +1 (217) 384.6330 support@powerworld.com
More informationDESIGNING POWER SYSTEM STABILIZER WITH PID CONTROLLER
International Journal on Technical and Physical Problems of Engineering (IJTPE) Published by International Organization on TPE (IOTPE) ISSN 20773528 IJTPE Journal www.iotpe.com ijtpe@iotpe.com June 2010
More informationSimulations and Control of Direct Driven Permanent Magnet Synchronous Generator
Simulations and Control of Direct Driven Permanent Magnet Synchronous Generator Project Work Dmitry Svechkarenko Royal Institute of Technology Department of Electrical Engineering Electrical Machines and
More informationFUZZY SLIDING MODE CONTROLLER FOR POWER SYSTEM SMIB
FUZZY SLIDING MODE CONTROLLER FOR POWER SYSTEM SMIB KHADDOUJ BEN MEZIANE, FAIZA DIB, 2 ISMAIL BOUMHIDI PhD Student, LESSI Laboratory, Department of Physics, Faculty of Sciences Dhar El Mahraz,Sidi Mohamed
More informationChapter 4. Synchronous Generators. Basic Topology
Basic Topology Chapter 4 ynchronous Generators In stator, a threephase winding similar to the one described in chapter 4. ince the main voltage is induced in this winding, it is also called armature winding.
More informationECE 421/521 Electric Energy Systems Power Systems Analysis I 3 Generators, Transformers and the PerUnit System. Instructor: Kai Sun Fall 2013
ECE 41/51 Electric Energy Systems Power Systems Analysis I 3 Generators, Transformers and the PerUnit System Instructor: Kai Sun Fall 013 1 Outline Synchronous Generators Power Transformers The PerUnit
More informationInternational Journal of Advance Engineering and Research Development SIMULATION OF FIELD ORIENTED CONTROL OF PERMANENT MAGNET SYNCHRONOUS MOTOR
Scientific Journal of Impact Factor(SJIF): 3.134 eissn(o): 23484470 pissn(p): 23486406 International Journal of Advance Engineering and Research Development Volume 2,Issue 4, April 2015 SIMULATION
More informationECE 325 Electric Energy System Components 7 Synchronous Machines. Instructor: Kai Sun Fall 2015
ECE 325 Electric Energy System Components 7 Synchronous Machines Instructor: Kai Sun Fall 2015 1 Content (Materials are from Chapters 1617) Synchronous Generators Synchronous Motors 2 Synchronous Generators
More informationSynchronous Machines
Synchronous Machines Synchronous generators or alternators are used to convert mechanical power derived from steam, gas, or hydraulicturbine to ac electric power Synchronous generators are the primary
More informationFuzzy Applications in a MultiMachine Power System Stabilizer
Journal of Electrical Engineering & Technology Vol. 5, No. 3, pp. 503~510, 2010 503 D.K.Sambariya and Rajeev Gupta* Abstract  This paper proposes the use of fuzzy applications to a 4machine and 10bus
More informationAn Introduction to Electrical Machines. P. Di Barba, University of Pavia, Italy
An Introduction to Electrical Machines P. Di Barba, University of Pavia, Italy Academic year 00 Contents Transformer. An overview of the device. Principle of operation of a singlephase transformer 3.
More informationLESSON 20 ALTERNATOR OPERATION OF SYNCHRONOUS MACHINES
ET 332b Ac Motors, Generators and Power Systems LESSON 20 ALTERNATOR OPERATION OF SYNCHRONOUS MACHINES 1 LEARNING OBJECTIVES After this presentation you will be able to: Interpret alternator phasor diagrams
More informationDynamic Modeling of Surface Mounted Permanent Synchronous Motor for Servo motor application
797 Dynamic Modeling of Surface Mounted Permanent Synchronous Motor for Servo motor application Ritu Tak 1, Sudhir Y Kumar 2, B.S.Rajpurohit 3 1,2 Electrical Engineering, Mody University of Science & Technology,
More informationSynchronous Machines
Synchronous machine 1. Construction Generator Exciter View of a twopole round rotor generator and exciter. A Stator with laminated iron core C Slots with phase winding B A B Rotor with dc winding B N S
More informationReduced Size Rule Set Based Fuzzy Logic Dual Input Power System Stabilizer
772 NATIONAL POWER SYSTEMS CONFERENCE, NPSC 2002 Reduced Size Rule Set Based Fuzzy Logic Dual Input Power System Stabilizer Avdhesh Sharma and MLKothari Abstract The paper deals with design of fuzzy
More informationSynchronous Machines
Synchronous Machines Synchronous Machines n 1 Φ f n 1 Φ f I f I f I f damper (runup) winding Stator: similar to induction (asynchronous) machine ( 3 phase windings that forms a rotational circular magnetic
More informationDynamics of the synchronous machine
ELEC0047  Power system ynamics, control an stability Dynamics of the synchronous machine Thierry Van Cutsem t.vancutsem@ulg.ac.be www.montefiore.ulg.ac.be/~vct These slies follow those presente in course
More informationDesign and Application of Fuzzy PSS for Power Systems Subject to Random Abrupt Variations of the Load
Design and Application of Fuzzy PSS for Power Systems Subject to Random Abrupt Variations of the Load N. S. D. Arrifano, V. A. Oliveira and R. A. Ramos Abstract In this paper, a design method and application
More informationEE2351 POWER SYSTEM ANALYSIS UNIT I: INTRODUCTION
EE2351 POWER SYSTEM ANALYSIS UNIT I: INTRODUCTION PART: A 1. Define per unit value of an electrical quantity. Write equation for base impedance with respect to 3phase system. 2. What is bus admittance
More informationEE2351 POWER SYSTEM ANALYSIS
EE351 POWER SYSTEM ANALYSIS A.Ahamed Riazudeen EEE DEPARTMENT 1 UNIT I INTRODUCTION Power system network 3 SINGLE LINE DIAGRAM It is a diagrammatic representation of a power system in which the components
More informationEE 451 Power System Stability
EE 451 Power System Stability Power system operates in synchronous mode Power system is subjected to a wide range of disturbances (small and large)  Loads and generation changes  Network changes  Faults
More informationREALTIME TRANSIENT STABILITY ASSESSMENT
CHAPTER 3 REALTIME TRANSIENT STABILITY ASSESSMENT In Chapter 2, the basic multimachine theory and the different dynamic, state and transient energy equations have been presented and the basic criterion
More informationGlobal Swing Instability in the New England Power Grid Model
9 American Control Conference Hyatt Regency Riverfront, St. Louis, MO, USA June , 9 ThC7. Global Swing Instability in the New England Power Grid Model Yoshihiko Susuki, Igor Mezić, Takashi Hikihara Abstract
More informationPhaseshifting transformers in a structurepreserving energy function
Electric Power Systems Research 74 (2005) 323 330 Phaseshifting transformers in a structurepreserving energy function A. Gabrijel a,, B. Mihalic b a EletroSlovenija, d.o.o., Hajdrihova 2, 1000 Ljubljana,
More informationChapter 2 Power System Voltage Stability and Models of Devices
Chapter 2 Power System Voltage Stability and Models of Devices Abstract This chapter introduces the concepts of voltage instability and the distinctions between voltage and angle instability. The driving
More informationLecture 1: Induction Motor
1 / 22 Lecture 1: Induction Motor ELECE8402 Control of Electric Drives and Power Converters (5 ECTS) Marko Hinkkanen Aalto University School of Electrical Engineering Spring 2016 2 / 22 Learning Outcomes
More informationControl Lyapunov Functions for Controllable Series Devices
IEEE TRANSACTIONS ON POWER SYSTEMS, VOL. 16, NO. 4, NOVEMBER 2001 689 Control Lyapunov Functions for Controllable Series Devices Mehrdad Ghandhari, Member, IEEE, Göran Andersson, Fellow, IEEE, and Ian
More informationResearch Paper ANALYSIS OF POWER SYSTEM STABILITY FOR MULTIMACHINE SYSTEM D. Sabapathi a and Dr. R. Anita b
Research Paper ANALYSIS OF POWER SYSTEM STABILITY FOR MULTIMACHINE SYSTEM D. Sabapathi a and Dr. R. Anita b Address for Correspondence a Research Scholar, Department of Electrical & Electronics Engineering,
More informationECE 422 Power System Operations & Planning 7 Transient Stability
ECE 4 Power System Operations & Planning 7 Transient Stability Spring 5 Instructor: Kai Sun References Saaat s Chapter.5 ~. EPRI Tutorial s Chapter 7 Kunur s Chapter 3 Transient Stability The ability of
More informationParameter Estimation of Three Phase Squirrel Cage Induction Motor
International Conference On Emerging Trends in Mechanical and Electrical Engineering RESEARCH ARTICLE OPEN ACCESS Parameter Estimation of Three Phase Squirrel Cage Induction Motor Sonakshi Gupta Department
More informationPOWER SYSTEM DYNAMIC STATE ESTIMATION and LOAD MODELING. Cem Bila
POWER SYSTEM DYNAMIC STATE ESTIMATION and LOAD MODELING A Thesis Presented by Cem Bila to The Department of Electrical and Computer Engineering in partial fulfillment of the requirements for the degree
More informationArtificial Bee Colony Based Power System Stabilizer Design for a TurboGenerator in a SingleMachine Power System
Artificial Bee Colony Based Power System Stabilizer Design for a TurboGenerator in a SingleMachine Power System H. Shayeghi H. A. Shayanfar A. Ghasemi Technical Eng. Department E.E.Department Center
More informationGeneralized Theory of Electrical Machines A Review
Generalized Theory of Electrical Machines A Review Dr. Sandip Mehta Department of Electrical and Electronics Engineering, JIET Group of Institutions, Jodhpur Abstract:This paper provides an overview
More informationPARAMETRIC ANALYSIS OF SHAFT TORQUE ESTIMATOR BASED ON OBSERVER
PARAMETRIC ANALYSIS OF SHAFT TORQUE ESTIMATOR BASED ON OBSERVER Tetsuro Kakinoki, Ryuichi Yokoyama Tokyo Metropolitan University t.kakinoki@h4.dion.ne.jp Goro Fujita Shibaura Institute of Technology Kaoru
More informationChapter 8: Unsymmetrical Faults
Chapter 8: Unsymmetrical Faults Introduction The sequence circuits and the sequence networks developed in the previous chapter will now be used for finding out fault current during unsymmetrical faults.
More informationLecture 8: Sensorless Synchronous Motor Drives
1 / 22 Lecture 8: Sensorless Synchronous Motor Drives ELECE8402 Control of Electric Drives and Power Converters (5 ECTS) Marko Hinkkanen Spring 2017 2 / 22 Learning Outcomes After this lecture and exercises
More informationThe Influence of Machine Saturation on Bifurcation and Chaos in Multimachine Power Systems
The Influence of Machine Saturation on Bifurcation and Chaos in Multimachine Power Systems Majdi M. Alomari and Jian Gue Zhu University of Technology, Sydney (UTS) P.O. Box 123, Broadway NSW 2007, Australia
More informationFLEXIBLE ac transmission system (FACTS) devices give
694 IEEE TRANSACTIONS ON POWER DELIVERY, VOL. 19, NO. 2, APRIL 2004 A NewtonType Current Injection Model of UPFC for Studying LowFrequency Oscillations Kwang M. Son, Member, IEEE, and Robert H. Lasseter,
More informationTransient Stability Improvement of Multimachine Power System Using Fuzzy Controlled TCSC
International Journal of Advancements in Research & Technology, Volume 1, Issue, July1 Transient Stability Improvement of Multimachine Power System Using Fuzzy Controlled TCSC GUNDALA SRINIVASA RAO,
More informationAC Circuits Homework Set
Problem 1. In an oscillating LC circuit in which C=4.0 μf, the maximum potential difference across the capacitor during the oscillations is 1.50 V and the maximum current through the inductor is 50.0 ma.
More information12 Chapter Driven RLC Circuits
hapter Driven ircuits. A Sources... . A ircuits with a Source and One ircuit Element... 3.. Purely esistive oad... 3.. Purely Inductive oad... 6..3 Purely apacitive oad... 8.3 The Series ircuit...
More informationAPPLICATIONS OF CONTROLLABLE SERIES CAPACITORS FOR DAMPING OF POWER SWINGS *
APPLICATIONS OF CONTROLLABLE SERIES CAPACITORS FOR DAPING OF POWER SWINGS *. Noroozian P. Halvarsson Reactive Power Compensation Division ABB Power Systems S7 64 Västerås, Sweden Abstract This paper examines
More informationTransients on Integrated Power System
Chapter 3 Transients on Integrated Power System 3.1 Line Dropping and Load Rejection 3.1.1 Line Dropping In three phase circuit capacitance switching, the determination of the voltage trapped after switching
More informationTransient stability improvement by using PSS and increasing inertia of synchronous machine
American Journal of Electrical Power and Energy Systems 2014; 3(2): 4549 Published online April 20, 2014 (http://www.sciencepublishinggroup.com/j/epes) doi:10.11648/j.epes.20140302.15 Transient stability
More informationTransient Analysis of Doubly Fed Wind Power Induction Generator Using Coupled FieldCircuit Model
Publication P2 Seman, S., Kanerva, S., Niiranen, J., Arkkio, A. 24. Transient Analysis of Wind Power Doubly Fed Induction Generator Using Coupled Field Circuit Model, Proceedings of ICEM 24, 58 September
More informationPower System Analysis
Power System Analysis Power Flow Analysis Fault Analysis Power System Dynamics and Stability Lecture 227052600, ITET ETH Zürich Göran Andersson EEH  Power Systems Laboratory ETH Zürich September 2012
More informationChapter 6. Induction Motors. Copyright The McGrawHill Companies, Inc. Permission required for reproduction or display.
Chapter 6 Induction Motors 1 The Development of Induced Torque in an Induction Motor Figure 66 The development of induced torque in an induction motor. (a) The rotating stator field B S induces a voltage
More informationModel of the Induction Machine including Saturation
Model of the Induction Machine including Saturation José M. Aller, Daniel Delgado, Alexander Bueno, Julio C. Viola and José A. Restrepo UNIVERSIDAD SIMÓN BOLÍVAR Valle de Sartenejas, Baruta, Edo. Miranda
More informationStudy of Transient Stability with Static Synchronous Series Compensator for an SMIB
Study of Transient Stability with Static Synchronous Series Compensator for an SMIB M.Chandu, Dr.T.R.Jyosthna 2 M.tech, Electrical Department, Andhra University, Andhra Pradesh, India 2 Professor, Electrical
More informationCHAPTER 5 SIMULATION AND TEST SETUP FOR FAULT ANALYSIS
47 CHAPTER 5 SIMULATION AND TEST SETUP FOR FAULT ANALYSIS 5.1 INTRODUCTION This chapter describes the simulation model and experimental set up used for the fault analysis. For the simulation set up, the
More informationFEEDBACK CONTROL SYSTEMS
FEEDBAC CONTROL SYSTEMS. Control System Design. Open and ClosedLoop Control Systems 3. Why ClosedLoop Control? 4. Case Study  Speed Control of a DC Motor 5. SteadyState Errors in Unity Feedback Control
More informationScanned by CamScanner
Scanned by CamScanner Scanned by CamScanner t W I w v 6.00fall 017 Midterm 1 Name Problem 3 (15 pts). F the circuit below, assume that all equivalent parameters are to be found to the left of port
More informationRevision Guide for Chapter 15
Revision Guide for Chapter 15 Contents tudent s Checklist Revision otes Transformer... 4 Electromagnetic induction... 4 Generator... 5 Electric motor... 6 Magnetic field... 8 Magnetic flux... 9 Force on
More informationTRANSIENT CURRENTS IN TURBOGENERATOR FOR THE SUDDEN SHORT CIRCUIT
Prace Naukowe Instytutu Maszyn, Napędów i Pomiarów Elektrycznych Nr 63 Politechniki Wrocławskiej Nr 63 Studia i Materiały Nr 29 29 Piotr KISIELEWSKI*, Ludwik ANTAL* synchronous machines, turbogenerators,
More informationDefinition Application of electrical machines Electromagnetism: review Analogies between electric and magnetic circuits Faraday s Law Electromagnetic
Definition Application of electrical machines Electromagnetism: review Analogies between electric and magnetic circuits Faraday s Law Electromagnetic Force Motor action Generator action Types and parts
More informationIEEE PES Task Force on Benchmark Systems for Stability Controls
IEEE PES Task Force on Benchmark Systems for Stability Controls Ian Hiskens November 9, 3 Abstract This report summarizes a study of an IEEE generator, 39bus system. Three types of analysis were performed:
More informationEDEXCEL NATIONALS UNIT 5  ELECTRICAL AND ELECTRONIC PRINCIPLES. ASSIGNMENT No. 3  ELECTRO MAGNETIC INDUCTION
EDEXCEL NATIONALS UNIT 5  ELECTRICAL AND ELECTRONIC PRINCIPLES ASSIGNMENT No. 3  ELECTRO MAGNETIC INDUCTION NAME: I agree to the assessment as contained in this assignment. I confirm that the work submitted
More informationA New Model Reference Adaptive Formulation to Estimate Stator Resistance in Field Oriented Induction Motor Drive
A New Model Reference Adaptive Formulation to Estimate Stator Resistance in Field Oriented Induction Motor Drive Saptarshi Basak 1, Chandan Chakraborty 1, Senior Member IEEE and Yoichi Hori 2, Fellow IEEE
More informationSESSION 3. Short Circuit Calculations, Unsymmetrical Faults. Leonard Bohmann, Michigan State University Elham Makram, Clemson University
SESSON Short Circuit Calculations, Unsymmetrical Faults Leonard Bohmann, Michigan State University Elham Makram, Clemson University Short Circuit Calculations Leonard Bohmann Michigan State University
More informationELG4125: Power Transmission Lines Steady State Operation
ELG4125: Power Transmission Lines Steady State Operation TwoPort Networks and ABCD Models A transmission line can be represented by a twoport network, that is a network that can be isolated from the
More informationA Decoupling Based Direct Method for Power System Transient Stability Analysis
A Decoupling Based Direct Method for Power System Transient Stability Analysis Bin Wang, Kai Sun Electrical Engineering and Computer Science University of Tennessee, Knoxville, TN USA bwang13@utk.edu,
More informationAC Induction Motor Stator Resistance Estimation Algorithm
7th WSEAS International Conference on Electric Power Systems, High Voltages, Electric Machines, Venice, Italy, November 2123, 27 86 AC Induction Motor Stator Resistance Estimation Algorithm PETR BLAHA
More informationSinusoidal SteadyState Analysis
Sinusoidal SteadyState Analysis Almost all electrical systems, whether signal or power, operate with alternating currents and voltages. We have seen that when any circuit is disturbed (switched on or
More informationEnhancement of transient stability analysis of multimachine power system
WWJMRD 2016; 2(6): 4145 www.wwjmrd.com Impact Factor MJIF: 4.25 eissn: 24546615 Oyediran Oyebode Olumide Department of Computer Engineering, Osun State Polytechnic Iree, Osun State, Nigeria Ogunwuyi
More informationSynchronous Machines  Structure
Synchronou Machine  Structure Synchronou Machine  Structure rotate at contant peed. primary energy converion device of the word electric power ytem. both generator and motor operation can draw either
More informationA simple model based control of self excited induction generators over a wide speed range
ISSN 1 7467233, England, UK World Journal of Modelling and Simulation Vol. 10 (2014) No. 3, pp. 206213 A simple model based control of self excited induction generators over a wide speed range Krishna
More informationChapter 33. Alternating Current Circuits
Chapter 33 Alternating Current Circuits 1 Capacitor Resistor + Q = C V = I R R I + + Inductance d I Vab = L dt AC power source The AC power source provides an alternative voltage, Notation  Lower case
More informationImpact of Model Detail of Synchronous Machines on Realtime Transient Stability Assessment
2013 IREP SymposiumBulk Power System Dynamics and Control IX (IREP), August 2530, 2013, Rethymnon, Greece Impact of Model Detail of Synchronous Machines on Realtime Transient Stability Assessment Tilman
More informationDynamic Modeling of Rotary Double Inverted Pendulum Using Classical Mechanics
ISBN 9789384468 Proceedings of 5 International Conference on Future Computational echnologies (ICFC'5) Singapore, March 93, 5, pp. 963 Dynamic Modeling of Rotary Double Inverted Pendulum Using Classical
More informationELG3311: Assignment 3
LG33: ssignent 3 roble 6: The Yconnected synchronous otor whose naeplate is shown in Figure 6 has a perunit synchronous reactance of 0.9 and a perunit resistance of 0.0. (a What is the rated input
More informationMagnetic Leakage Fields and End Region Eddy Current Power Losses in Synchronous Generators
Digital Comprehensive Summaries of Uppsala Dissertations from the Faculty of Science and Technology 1575 Magnetic Leakage Fields and End Region Eddy Current Power Losses in Synchronous Generators BIRGER
More informationTransient Analysis of Three Phase Squirrel Cage Induction Machine using Matlab
Transient Analysis of Three Phase Squirrel Cage Induction Machine using Matlab Mukesh Kumar Arya*, Dr.Sulochana Wadhwani** *( Department of Electrical Engineering, Madhav Institute of Technology & Science,
More informationThe Enlarged dq Model of Induction Motor with the Iron Loss and Saturation Effect of Magnetizing and Leakage Inductance
The Enlarged dq Model of Induction Motor with the Iron Loss and Saturation Effect of Magnetizing and Leakage Inductance Jan Otýpka, Petr Orság, Vítězslav Stýskala, Dmitrii Kolosov, Stanislav Kocman and
More informationTRANSIENT STABILITY ANALYSIS OF POWER SYSTEMS WITH ENERGY STORAGE
TRANSIENT STABILITY ANALYSIS OF POWER SYSTEMS WITH ENERGY STORAGE by CHI YUAN WENG Submitted in the partial fulfillment of the requirements For the degree of Master of Science Thesis Advisor: Dr. Kenneth
More information11.1 Power System Stability Overview
11.1 Power System Stability Overview This introductory section provides a general description of the power system stability phenomena including fundamental concepts, classification, and definition of associated
More informationControl of an Induction Motor Drive
Control of an Induction Motor Drive 1 Introduction This assignment deals with control of an induction motor drive. First, scalar control (or VoltsperHertz control) is studied in Section 2, where also
More informationExtension of the Complex Torque Coefficient Method for Synchronous Generators to Auxiliary Devices in Electrical Networks
Extension of the Complex Torque Coefficient Method for Synchronous Generators to Auxiliary Devices in Dr. SWISS FEDERAL INSTITUTE OF TECHNOLOGY Electrical Engineering Department, Laboratory of Electromechanics
More informationVirtual Inertia: Current Trends and Future Directions
applied sciences Review Virtual Inertia: Current Trends and Future Directions Ujjwol Tamrakar 1, Dipesh Shrestha 1, Manisha Maharjan 1, Bishnu P. Bhattarai 2, Timothy M. Hansen 1 and Reinaldo Tonkoski
More informationThe basic principle to be used in mechanical systems to derive a mathematical model is Newton s law,
Chapter. DYNAMIC MODELING Understanding the nature of the process to be controlled is a central issue for a control engineer. Thus the engineer must construct a model of the process with whatever information
More informationAn Approach to Design and Simulate Synchronous Machine with Excitation System Modeling
International Journal of Scientific and Research Publications, Volume, Issue 7, July ISSN 55 An Approach to Design and Simulate Synchronous Machine with Excitation System Modeling MUHAMMAD SHAHID, AZIZ
More informationME 375 Final Examination Thursday, May 7, 2015 SOLUTION
ME 375 Final Examination Thursday, May 7, 2015 SOLUTION POBLEM 1 (25%) negligible mass wheels negligible mass wheels v motor no slip ω r r F D O no slip e in Motor% Cart%with%motor%a,ached% The coupled
More information2 NETWORK FORMULATION
NTWRK FRMUATN NTRDUCTRY RMARKS For performing any power system studies on the digital computer, the first step is to construct a suitable mathematical model of the power system network The mathematical
More informationAMONG POWER SYSTEM CONTROLS IMPACT OF INTERACTIONS EPRI/NSF WORKSHOP PLAYACAR, APRIL 2002 GLOBAL DYNAMIC OPTIMISATION OF THE ELECTRIC POWER GRID
EPRI/NSF WORKSHOP PLAYACAR, APRIL 00 GLOBAL DYNAMIC OPTIMISATION OF THE ELECTRIC POWER GRID IMPACT OF INTERACTIONS AMONG POWER SYSTEM CONTROLS NELSON MARTINS JULIO C.R. FERRAZ, SERGIO GOMES JR. CEPEL COPPE/UFRJ
More informationSTEADYSTATE MODELING AND ANALYSIS OF THREE PHASE SELFEXCITED INDUCTION GENERATOR WITH SERIES COMPENSATION
STEADYSTATE MODELING AND ANALYSIS OF THREE PHASE SELFEXITED INDUTION GENERATOR WITH SERIES OMPENSATION S. Singaravelu and S. Sasikumar Department of Electrical Engineering, Annamalai University, hidambaram,
More informationTurbines and speed governors
ELEC0047  Power system dynamics, control and stability Turbines and speed governors Thierry Van Cutsem t.vancutsem@ulg.ac.be www.montefiore.ulg.ac.be/~vct November 2017 1 / 31 2 / 31 Steam turbines Turbines
More informationOverview of motors and motion control
Overview of motors and motion control. Elements of a motioncontrol system Power upply Highlevel controller owlevel controller Driver Motor. Types of motors discussed here; Brushed, PM DC Motors Cheap,
More informationAnalyzing the Effect of Ambient Temperature and Loads Power Factor on Electric Generator Power Rating
Analyzing the Effect of Ambient Temperature and Loads Power Factor on Electric Generator Power Rating Ahmed Elsebaay, Maged A. Abu Adma, Mahmoud Ramadan Abstract This study presents a technique clarifying
More informationModeling and Simulation of FluxOptimized Induction Motor Drive
Research Journal of Applied Sciences, Engineering and Technology 2(6): 603613, 2010 ISSN: 20407467 Maxwell Scientific Organization, 2010 Submitted Date: July 21, 2010 Accepted Date: August 20, 2010 Published
More informationUNITI Economic Operation of Power Systems 1
UNITI Economic Operation of Power Systems 1 Overview Economic Distribution of Loads between the Units of a Plant Generating Limits Economic Sharing of Loads between Different Plants Automatic Generation
More informationSmallSignal Analysis of a Saturated Induction Motor
1 SmallSignal Analysis of a Saturated Induction Motor Mikaela Ranta, Marko Hinkkanen, AnnaKaisa Repo, and Jorma Luomi Helsinki University of Technology Department of Electrical Engineering P.O. Box 3,
More informationIntroduction. Energy is needed in different forms: Light bulbs and heaters need electrical energy Fans and rolling miles need mechanical energy
Introduction Energy is needed in different forms: Light bulbs and heaters need electrical energy Fans and rolling miles need mechanical energy What does AC and DC stand for? Electrical machines Motors
More informationON THE PARAMETERS COMPUTATION OF A SINGLE SIDED TRANSVERSE FLUX MOTOR
ON THE PARAMETERS COMPUTATION OF A SINGLE SIDED TRANSVERSE FLUX MOTOR Henneberger, G. 1 Viorel, I. A. Blissenbach, R. 1 Popan, A.D. 1 Department of Electrical Machines, RWTH Aachen, Schinkelstrasse 4,
More informationGATEFORUM India s No.1 institute for GATE training 1
EEGATE03 PAPER Q. No. 5 Carry One Mark Each. Given a vector field F = y xax yzay = x a z, the line integral F.dl evaluated along a segment on the xaxis from x= to x= is .33 (B) 0.33 (D) 7 : (B) x 0.
More informationSTABILITY ANALYSIS AND OPTIMAL CONTROL DESIGN FOR ACDC POWER SYSTEM WITH CONSTANT POWER LOAD
STABILITY ANALYSIS AND OPTIMAL CONTROL DESIGN FOR ACDC POWER SYSTEM WITH CONSTANT POWER LOAD by JeanMarc Coulomb B.S. in Electrical Engineering, ESIGELEC, 2011 Submitted to the Graduate Faculty of the
More information