Aalborg Universitet. Published in: Mathematics and Computers in Simulation. DOI (link to publication from Publisher): /j.matcom


 Maryann Brooks
 10 months ago
 Views:
Transcription
1 Aalborg Univeritet Grid impedance etimation baed hybrid ilanding detection method for AC microgrid Ghzaiel, Walid ; JebaliBen Ghorbal, Manel; SlamaBelkhodja, Ilhem ; Guerrero, Joep M. Publihed in: Mathematic and Computer in Simulation DOI (link to publication from Publiher):.6/j.matcom.5..7 Publication date: 7 Document Verion Early verion, alo known a preprint Link to publication from Aalborg Univerity Citation for publihed verion (APA): Ghzaiel, W., JebaliBen Ghorbal, M., SlamaBelkhodja, I., & Guerrero, J. M. (7). Grid impedance etimation baed hybrid ilanding detection method for AC microgrid. Mathematic and Computer in Simulation, 3, DOI:.6/j.matcom.5..7 General right Copyright and moral right for the publication made acceible in the public portal are retained by the author and/or other copyright owner and it i a condition of acceing publication that uer recognie and abide by the legal requirement aociated with thee right.? Uer may download and print one copy of any publication from the public portal for the purpoe of private tudy or reearch.? You may not further ditribute the material or ue it for any profitmaking activity or commercial gain? You may freely ditribute the URL identifying the publication in the public portal? Take down policy If you believe that thi document breache copyright pleae contact u at providing detail, and we will remove acce to the work immediately and invetigate your claim. Downloaded from vbn.aau.dk on: januar 9, 8
2 Accepted Manucript Grid impedance etimation baed hybrid ilanding detection method for AC microgrid Walid Ghzaiel, Manel Jebali Ben Ghorbal, Ilhem Slama Belkhodja, Joep M. Guerrero PII: S (5)9 DOI: Reference: MATCOM 453 To appear in: Mathematic and Computer in Simulation Received date: October 4 Revied date: 8 Augut 5 Accepted date: 6 October 5 Pleae cite thi article a: W. Ghzaiel, M. Jebali Ben Ghorbal, I. Slama Belkhodja, J.M. Guerrero, Grid impedance etimation baed hybrid ilanding detection method for AC microgrid, Math. Comput. Simulation (5), Thi i a PDF file of an unedited manucript that ha been accepted for publication. A a ervice to our cutomer we are providing thi early verion of the manucript. The manucript will undergo copyediting, typeetting, and review of the reulting proof before it i publihed in it final form. Pleae note that during the production proce error may be dicovered which could affect the content, and all legal diclaimer that apply to the journal pertain.
3 Manucript Click here to view linked Reference Grid impedance etimation baed hybrid ilanding detection method for AC microgrid Walid Ghzaiel a, Manel Jebali Ben Ghorbal a, Ilhem Slama Belkhodja a and Joep M. Guerrero b a Univerité de Tuni El Manar, ENIT, L.S.E., LR ES 5, BP 37, Tuni le Belvédère, Tuniie b Aalborg Univerity, Dept. Energy Technology, 9 Aalborg, Denmark Abtract Thi paper focue on a hybrid ilanding detection algorithm for parallelinverterbaed microgrid. The propoed algorithm i implemented on the unit enuring the control of the intelligent bypa witch connecting or diconnecting the microgrid from the utility. Thi method employ a grid impedance etimation technique that ue reonance excitation once grid fault occur. It include two tage: the firt one i to detect grid impedance variation reulting from a grid fault; and the econd one i to excite the reonance by uing a virtual reitance in order to extract the grid impedance parameter. Grid impedance variation detection algorithm i baed on grid current meaurement temporal redundancie with fat current acquiition period. Once the grid impedance variation i detected, the excitation reonance i performed by injecting a reonance frequency in only one inverter control to avoid interaction with other unit. The elected inverter will be the one cloet to the controllable ditributed generation ytem or to a healthy grid ide in cae of mehed microgrid with multiplegrid connection. The detection algorithm i applied to quickly detect the reonance phenomena, o that the reonance excitation i canceled and the reitive and inductive grid impedance part are etimated. Simulation reult are carried out to illutrate the effectivene of the propoed method. Keyword: microgrid, ilanding, grid impedance variation, reonance excitation, droop control method, virtual reitance.. Introduction Microgrid (MG) are emerging a a way to improve both power quality of the electrical grid by making them marter and more flexible in the future. MG hould be able to operate connected to the utility grid or in iland under grid fault condition [6. The tranition between gridconnected and ilanded mode relie on the ilanding detection algorithm. The ilanding operation depend on the electrical power quality at the point of common coupling (PCC) and the grid exitence. Hence, two ilanding cenario can be conidered:  Intentional or preplanned ilanding: Symmetrical or unymmetrical fault taking place omewhere in the grid will lead to voltage dip, frequency variation or unbalance problem that can be nondetected by the protection device. In thi cae, local ilanded detection algorithm are needed to diconnect the MG.  Nonintentional or unplanned ilanding: In thi cae, MG continue to upply local load, while the main grid i diconnected from the PCC [8. A nondetected ilanding condition may lead to dangerou ituation for utility peronnel and caue damage to the ditributed generation ytem compoing the MG. Hence, a reliable ilanding detection method hould be et in order to detect any ilanding cenario at leat a fat a required by tandard. German tandard (VDE 6), for example, require diconnection from the utility grid under grid impedance variation of Ω within 5 [. The detection hould be available even under the wort condition defined a a NonDetection Zone (NDZ), in which MG active and reactive produced power are completely conumed by the load. In fact, pre
4 planned ilanding could be eaily detected by repecting ome tringent predefined tandard. However, unplanned ilanding, that i to ay the failure of the grid, i more complicated to be detected ince the voltage and frequency at PCC can be utained in NDZ limit. In the literature, everal method have been propoed for ilanding detection due to the importance of thi iue and it impact on the interconnected ytem behavior [9,, 4, 3, 8, 6. Thee method are mainly divided into two main categorie: communicationbaed method between the protection device and the power generation ytem, and local method that ue only local meaurement. Local method can be claified into three ubcategorie: paive method challenged by a large NDZ and an accurate uitable threhold; active method that uffer from power quality degradation; and hybrid method that tend to ummarize the benefit of both paive and active method. In thi ene, a novel hybrid ilanding detection method baed on grid current meaurement and reonance excitation i propoed in thi paper. Indeed, at firt, a paive method baed on continuou grid current meaurement allow the detection of any abrupt grid current variation at the PCC. Afterward, thi paive method i combined with an active method baed on the injection of the proper reonance frequency. Reonance excitation i carried out by implementing and varying a virtual reitance. Thi reitance help, in grid connected mode, to improve the output power quality in healthy grid mode and to drive the ytem near the reonance once an abrupt grid current variation i detected. It alo allow the dicrimination of the variation caue: grid impedance variation [3 or load variation. Thi method i able to detect ilanding condition under any faulty condition even under the NDZ, the wort cae, where other method failed [8. However, in a MG that comprie parallel inverter connected to the grid, the method application i more difficult due to the different proper reonance frequencie reulting from the impedance of each generation ytem. A conequence, reonance excitation of each inverter can damage the ytem and reduce the reliability of the MG. To overcome thi problem, a MG control tructure i propoed which derived from the tructure of the parallelinverter connected to double grid: the grid fault occurrence detection algorithm allow tiff grid determination and faulty grid one. Afterward, in reonance excitation phae, only the cloet ditributed generation ytem (DGS) to the healthy grid remain connected to thi utility grid while the other are diconnected. However, they are kept interconnected with controllable DGS, uch a ga engine, dieel generator or ditributed torage ytem. Thee controllable DGS can upport voltage and frequency in ilanded mode. The developed grid impedance parameter determination algorithm will be executed by the healthy grid cloet DGS control. Thi paper i organized a follow. The double gridconnected MG tructure and the propoed MG control tructure are reported in ection II. The hybrid ilanding method i introduced and dicued in ection III with the different algorithm tep. Section IV i devoted to imulation reult.. Microgrid architecture and control trategy MG generally include parallel ditributed generation ytem modeled by threephae inverter connected to the utility grid through an LCLfilter for the noncontrollable DGS and LCfilter for the controllable DGS. For implicity, LCLfilter are ued for both type of DGS in thi paper. The grid ide filter inductance i conidered a a line inductance, which increae the inductive character of output ytem impedance and help for a proper parallel operation of controllable DGS ince they operate a voltage ource... Microgrid with two grid connection point For a mehed MG, the MG can be connected to a double grid through two intelligent bypa witche (IBS) in order to enure better ervice continuity under grid fault. Fig. preent a double gridconnected MG tructure: parallelinverter and load remain gridconnected when gridcondition guarantee a proper operation. In cae of grid fault occurrence detected on one ide of the double grid, the witche Ki, i =,...4 will cloe and open according to the grid failure in order to enure healthy working of load and DGS and afety tranfer of the electrical energy.
5 The propoed ilanding method i baed on a reonance injection for a pecific period. Thi will have a negative impact due to the interaction between the parallelinverter under reonance tate. Thi interaction i a conequence of the line impedance between each inverter and the AC common bu. A a olution, an inverter with load can remain connected to the healthy grid, wherea the other DGS excite the reonance to determine the grid impedance of the faulty grid. Hence, the etimated impedance value help keeping the witch tate deciion... Propoed microgrid tructure A controllable DGS (DG3), uch a ga engine, dieel generator and ditributed torage ytem, i included. It i connected to parallel inverter and behave like a grid tracker in order to upport the voltage and frequency in ilanded mode. The noncontrollable DGS are inverter baed on renewable power ource uch a wind turbine (WTS) and photovoltaic ytem (PVS). They act a current ource in grid connection mode. The ytem compoed of controllable DGS, noncontrollable DGS (DG) and load, i connected to the cloet DGS from the grid (DG) through a witch device noted K and all the ytem i connected to the grid through an IBS, a depicted in Fig.. Indeed, grid impedance variation challenge the AC bu interfacing inverter control. In thi way, the witch K hould be opened once a grid impedance variation wa detected to avoid reonance problem in the MG caued by the interaction with the grid. Hence, controllable DG will, together with the parallel inverter DG, upply the load while the cloet DG will execute the algorithm of grid impedance parameter determination to detect the ilanding condition. A a conequence, different poible cenario can occur a illutrated in Table. Table. Propoed MG cenario IBS K Scenario ON ON Connected MG ON OFF Connected DG ON Off ReON OFF Reconnected MG Ilanded MG 3 Fig.. Configuration of a MG connected to a doublegrid Fig.. Propoed MG tructure control trategy
6 3. Propoed microgrid control trategy 4 In gridconnected mode, parallel noncontrollable DGS, uch a PVS and WTS, behave like current ource (CS). Their control require maximum power point tracking (MPPT) algorithm in order to ufficiently upply the load and to inject the maximum power to grid. In thi gridconnected mode, both frequency and voltage are upported by the grid. The controllable DGS act a a voltage tracker, behaving like a voltage ource, where it reference are the grid voltage and frequency [8. In ilanded mode and during the execution of the algorithm explained hereinafter, the controllable DGS will change it reference to upport by itelf the voltage and frequency while the parallel noncontrollable DGS are till working a current ource. Indeed, MG i uually deigned o a to repect the following relation in order to avoid tranmiion power loe a follow P P and Q Q () MG Load However, in ilanded mode, and with noncontrollable DGS baed on MPPT, the produced MG power hould not exceed the total demanded load power. In thi way, the intalled noncontrollable DGS hould have a maximum power le than the minimum total load power a follow P P () Load _ min DG _ max Q Load _ min QDG _ max (3) The upported controllable DG act hence a a grid ource and a power balancer. 3.. Noncontrollable DGS trategy A the noncontrollable DGS behave like a current ource, it control trategy i baed on controlling the grid ide current. The voltage and frequency are impoed by the grid in gridconnected mode and upported by the controllable DGS in ilanded mode. The continuou DC voltage i conidered a contant by a prime ource ide converter and the grid model i an inductive reitive branch in erie with an ideal voltage ource noted V g [8,. Noteworthy that the high order LCLfilter can provoke the ytem intability which need the integration of a damping element. For thi reaon, active damping i adopted a a olution and it i carried out by implementing a virtual reitance in the control trategy. In fact, it i done by multiplying the ened filtercapacitor current by a predetermined gain noted R v [3, and the reult of thi multiplication i ubtracted from the converter voltage reference a depicted in Fig. 3. In the propoed microgrid tructure, DG; in which the propoed ilanding detection algorithm i implemented and DG have the ame current control trategy. MG Load 3 Bode Diagram [ T [ T [ T G iex () Fig. 3. Noncontrollable DGS control trategy M a g n itu d e (d B ) P h a e (d e g ) Frequency (Hz) Wc=5 Wc= Wc=5 Fig. 4. Bode plot of multifrequencie nonideal PR For reliability and power quality reaon, a multifrequencie nonideal ProportionalReonant (PR) controller i ued to control the output current in both DG and DG. It good regulation capability and it
7 harmonic uppreion effect are proven in [3. In the noncontrollable DGS reponible for reonance excitation DG, the tranfer function of the adopted (PR) controller i given by: G ( ) = k iex pex krex ωc ω ω c k ω rexh c h= 5,7, ωc ω h where k pex i the proportional gain reponible for the ytem dynamic while k rex i the reonant gain reponible for reducing the teadytate error. ω, ω h, and ω c are repectively the fundamental frequency, the harmonic frequencie and the cutoff frequency ued for frequency fluctuation reducing a depicted in Fig. 4. For more implification, gridide current and reference voltage are expreed in the tationary reference a depicted in Fig. 3 uing the Concordia tranformation: = [ T V abc and i = [ T i abc [ = T [ T V 3.. Controllable DGS control trategy = In gridconnected controllable DGS; conidered a a voltage ource, the active and reactive power noted (P and Q) flowing from the filter output to the PCC through an inductor can be expreed a follow [7, 5: E V V E V P = ( coφ ) coθ in φ in θ (5) Z Z Z EV V EV Q = ( coφ )inθ in φ coθ (6) Z Z Z φ i the angle phae between the controllable DG filter output and the PCC, Z i the inductor impedance, E i the DGS capacitor voltage amplitude, V i the PCC voltage amplitude and θ i the inductor impedance angle. In thi paper, droop method i ued to control the controllable DGS and it principle i baed on the two following aumption: ) The inductor impedance i purely inductive (Z=X, θ=9 ). Thi aumption i true due to the large filtre inductance and power line impedance. But the reitive character of the power line impedance in low voltage cae can be a challenge. A a olution, virtual impedance can be added to the ytem control loop or uing LCLfilter intead of LC one. ) The angle φ i very mall and aumed to be null (φ =, coφ =). Baed on thee two aumption, Eq. (5) and Eq. (6) can be expreed a hown below, where the DGS frequency i ued intead of it angle phae ω = ω * m( P P*) (7) E = E * n( Q Q*) (8) From Eq. (5) and Eq. (6), the relation P/f and Q/E can be deduced. In fact, an increae in the active and reactive power lead to a decreae in the frequency and the voltage level repectively a can be hown in Fig. 5. Hence, the frequency and voltage can be conidered a information about demanded power load variation hared between the parallel inverter in real time. However, the conventional droop method ha the challenge of a low tranient repone. In thi ene, everal (4) 5
8 modified droop method have been propoed in literature [4, 7, 5. In thi paper, derivative and integrator term are added in droop equation to improve the ytem tranient repone. Hence, the equation will be expreed a: d( P P*) ω = ω * m( P P*) md (9) φ = φ * G p ( )( P P*) () dt E = E * n( Q Q*) nd ( Q Q*) () E = E * Gq ( )( Q Q*) () ɸ i the phae of the V c *, φ * = ω * dt = ω * t, md m G p ( ) = (3) nd n Gq ( ) = (4) E ω * ω ω 6 Fig. 5. Voltage and frequency droop principle [ T [ T Fig.6. Controllable DGS control trategy [ T G ( ) G i () G v () G q ( ) [ T [ T [ T LPF p ω* φ* φ V * in( ) c = E φ
9 7 Fig. 7. Control tructure baed on Droop control Droop control input, active and reactive power, are calculated from the unfiltered p and q power rich in ripple uing firt order lowpafilter (LPF) a expreed in Eq. (5) and Eq. (6). ωc p = Vc α iα Vcβ iβ P = p (5) ω c ωc q = Vc β iα Vcα iβ Q = q (6) ω c The three voltage reference i deduced from the etimated voltage amplitude E* and frequency ɸ a hown in Fig. 6 and it can be given by: Vc* = Ein( ωt) (7) The filter capacitor voltage and inverter current are both regulated by multifrequencie nonideal PR controller where it tranfer function i preented by: G ( ) = k v pv k ω rv c ω ω c k ω rvh c h= 5,7, ω c ω h (8) G( ) = k i pi kri ωc ω ω c k ω rih c h= 5,7, ω c h ω (9) 3.3. Synchronization Many grid ynchronization algorithm exit in the literature and their importance i growing due to it advanced role in performing an accurate ynchronization and avoiding overcurrent. One of thee ynchronization algorithm i the econd order generalized integrator SOGI that i adopted in thi paper ince it i characterized by it high efficiency under unbalance or perturbation a proven in literature [ and [3. The SOGI behave like a band pa filter with reonance frequency equal to the grid frequency (f=5hz), hence it i capable to extract the poitive and negative component. The poitive anglephae component i ued to ynchronize properly the MG. However, the grid frequency can be varied; hence an adaptive frequency loop named FLL block (frequency locked loop) i added to adapt the reonance frequency of the SOGI in real time. The SOGI algorithm conit of two filter; a band pa filter allowing the recontitution of the filtered input ignal V and a low pa filter permitting the contitution of the inquadrature component qv. The tranfer function of the econd order generalized integrator relating V a well a qv to the V i given by V ' k ω' = () V k ω' ω' qv V ' = k ω' k ω' ω' Where ɷ i the SOGI reonance frequency and k i the damping factor. V ocillate with the ame frequency ɷ of the input voltage while qv i the inquadrature component of V. Thee two parameter (V and qv ) are ued to calculate the poitive and negative equence for three phae ytem, while they are themelve the poitive and negative equence in ingle phae ytem, and to calculate the proper ()
10 anglephae. 8 ω' γ V abc [ T V α V β K K ω ff qvα' qvβ' FLL V β ' qvβ' Poitive equence αv ' V / α / / / / V β V α V β Negative equence Arctg(y/x) θ Arctg(y/x) θ Fig. 8. Threephae SOGIFLL algorithm 3.4. Hybrid ilanding method The propoed ilanding detection method i baed on two part, the firt one aim to detect the variation of grid impedance parameter while the econd one allow the determination of the grid impedance variation: A. Paive part: The method baed on temporal redundancie of grid current meaurement i widely ued and it efficiency in fault detection wa proven [. It principle conit on the detection of any abrupt variation between conecutive grid current meaurement. Any abrupt current variation will be depicted a a reidual with different amplitude level. Indeed, in healthy tate, with no grid impedance variation, the meaured quantity current evolution ha no dicontinuity, hence the final reidual noted Re igk, calculated from three conecutive nonfiltered reidual noted r k i lower than a mall threhold ε. Once the grid impedance varie, in faulty tate, the meaured current quantity evolution will preent a dicontinuity hown a a reidual pike at the intant of the grid fault. The reidual expreion are given by Eq. () and Eq. (3). Re () igk = rk rk rk r (3) k = igk igk igk i gk, i gk and i gk are the conecutive meaured current at the acquiition ampling time T a ; k T a, (k) T a and (k) T a. The threhold ε i defined a the maximum value that can reach Re igk when current evolution ha no dicontinuity (Re igk,< ε ) and ince it i proportional to the quare of the ampling, it will be alway very mall a expreed in Eq. (4) and Eq. (5). ε = 3ω Ta I m (4) I m VPCCm Vgm = (5) Z g Where VPCCm i the maximum voltage at PCC, Vgm i the maximum grid voltage, and τ ( ω = π / τ ) i the ytem time contant, with τ <<< Ta.
11 B. Active part: A proven in [3, the ytem reonance frequency depend on the grid impedance, epecially on the inductive part of the grid impedance. The active part of the propoed hybrid ilanding detection method allow the injection of the proper ytem reonance frequency needed to etimate the grid impedance parameter value once a grid fault occur. In fact, the reonance i excited properly by a virtual damping reitance noted R v that drive the ytem near the reonance once a reidual pike i detected. Indeed, the principle of the method conit on taking a high proportional gain in the beginning, and then reducing the virtual reitance gradually until reaching the reonance. Then, in the next tep the reonance frequency can be extracted by uing the Fat Fourier Tranformation (FFT). The reonance frequency of cloet DGS reponible for ilanding detection (indicated a part I in Fig.9), the etimated grid inductive part and the deduced grid reitive part are expreed a follow: 9 f re L L Lline Lg = (6) π L ( L L L ) C line g f Λ ( L L L L = g line (4π L Cf fre ) (4π L ( L L ) line ) C f fre ) (7) Λ R g = 4 9ω Ta ε 4 ( V PCCm V gm ) ( ωl ) g (8) 4. Simulation reult Simulation were carried out by uing PSIM oftware. The propoed ilanding detection method decribed for detection and etimation of grid impedance variation i teted on the ytem depicted in Fig.9. The parallelinverter and different kind of local load are connected to a PCC. The linear reitive load i continuouly connected but the linear reitiveinductive load (L_L) i connected at t ON =.8 and the nonlinear one at t ON =.. The load are ized to tet their effect on ilanding algorithm. The ytem parameter ued in imulation are hown in Table, 3 and 4. In the econd and third cenario, the voltage and frequency reference are propoed by the ytem itelf with E ref =35V and ɷ ref =34.59 rad/. Table. DGS parameter PDG PDG PDG3 VDC(V) fpwm L L Cf Zg Zd kw kw 4kW 65 khz mh mh 5µ.4Ω,.9mH mh Table 3. Load parameter Rp Rl Ll Rnl Lnl Cnl 55Ω 8Ω.4H 8Ω.4H µf Table 4. Control parameter k pex k iex k p k i k pv k iv ω c ω f R v m md n nd T a µ
12 DG Zline3 Zline [ T [ T [ T [ T [ T PWM PW M [ T  () G v  () G i () G i  [ T ON at t=. G q ( ) G p ( ) Gridconnected Microgrid φ* φ * E in( φ ) V c = Threhold DG ON at t=.8 Zline E = E * ω = ω* Q DG *= P DG *= Pule witch Reaching Reonance calculation Zg variation detection FFT etimation L g etimation R g L g PW M [ T  [ T Ilanding Algorithm [ T E= E g ω = ω g Q DG = Q DG * P DG= P DG * calculation Routh criteria Z gk in limit Ilanded Microgrid Z g : calculation algorithm G iex ()  Fig.9. Propoed MG control tructure An abrupt grid fault i carried out by varying the grid impedance (from Z g to Z g Z d ) at t=.4. The implemented paive part of the propoed ilanding method baed on reidual calculation detect thi variation uccefully by preenting a reidual pike. Then, the witch K i opened to iolate the part of ytem compoed of the cloet DGS from the grid (DG), the controllable DG and the noncontrollable DG from the whole microgrid ytem. Finally, the active part of the propoed hybrid method i applied by exciting the reonance a hown in Fig..
13 After the excitation during a pecific period choen here time of T ampling, the algorithm will take the appropriate deciion; recloing the witch K to reconnect the whole microgrid to the grid (cenario3) or going to cenario 4 and diconnect it from the utility grid to operate in ilanding mode. A Z d =mh, which preent an impedance variation of.638ω ( Z g < Ω), the witch K i recloed and cenario 3 i achieved. Noteworthy that before recloing the witch K, the adaptive virtual reitance R v can change it value to reconfigure the ytem with the new grid impedance parameter to maintain the ytem power quality. Fig. how the pectral analyi of the noncontrollable DG current output. A pike at the frequency f=86hz i preented. Thi frequency correpond to the excited reonance frequency. Hence, the new grid impedance i etimated (f re =86Hz Etimated L g =.7mH ) Fig. preent the active and reactive power of the noncontrollable DGand DG acting a a current ource and the controllable DG. The active power of noncontrollable DGS are et to kw, PD=PD=kW, while the controllable active power reference i choen 4kW. A hown in Fig., in gridconnected controllable DGS, there i nogrid impedance variation and K i cloed. In thi cae, the controllable DGS propoe it power reference. In cenario, under reonance excitation, the load require the needed power, hence the active P DG and reactive Q DG power do not track their reference and they jut inject the ret of the required load power none upplied by DG igdg igdg ig3dg Igref_DG Igref_DG Igref3_DG reidual pulewitch k Time () Fig.. Zg variation detection and reonance excitation IgDG IgDG Ig3DG 5 5 Frequency (Hz) Fig.. Reonance frequency (Zd=mH) Pulewitch k Pulewitch k.8.4 PDG PDG 4 3 PDG Pref 4.5K 4K 3.5K 3K.5K QDG Qref K K K K K.8..4 Time () Fig.. DGS output during the tranition between cenario Reigk 8 4 Vca_ref Vcb_ref Vcc_ref VCDG_a VCDG_b VCDG_c E_reference Time () Fig. 3. Controllable DGS output voltage during reonance
14 The LCLfilter capacitor voltage in the controllable DGS noted by V c i illutrated in Fig. 3, where the reonance effect doe not appear. It amplitude follow the voltage amplitude obtained at the output of the droop control algorithm, noted a Ereference. Ereference decreae during the reonance tate due to the change of voltage amplitude reference a preented in Fig. 9, part Control algorithm. It hould be noted that the reonance excitation duration i choen here, and in all next imulation reult, equal to 8 time the T ampling. Thi duration i lower than the time required by tandard (.) to detect ilanding mode. It depend on the period of FFT window that neceitie N ( N =6, 56, 5 ) ampling time and can be le than the choen duration. Indeed, the choice of thi long period aim to how up the capability of the virtual reitance for reonance controlling by puhing the ytem near the reonance without diverge. Fig. 4 how the voltage at PCC upported by the controllable DGS under reonance excitation and by the utility grid over the reonance. The PCC voltage track it reference, noted E pcc, reduced during the reonance tate due to the diconnection of the controllable DG3 from the utility grid and to it relation to the reactive power demanded by the load. Notice that the frequency preent a little variation in thi tate due to the relation P/f with the active power conumed by the load. Pulewitch k Vpcc_a Vpcc_b Vpcc_c Epcc Wpcc Time () Fig.4. PCC voltage and frequency during reonance excitation Reigk 8 4 igdg igdg ig3dg Igref_DG Igref_DG Igref3_DG   Ia_lr Ib_lr Ic_lr Ia_ll Ib_ll Ic_ll Time () Fig. 5. Load power quality during algorithm execution A preented in Fig. 5, linear reitive and reitiveinductive load are connected to the AC bu at different time to emphaize the effect of an abrupt load variation on the ilanding detection method. The imulation reult how that the propoed ilanding detection method doe not have any negative effect on the load current. 6K 5K PRPLL PDGPDG IgSG IgDG Ig3DG 4K 3K K QDGQDG 4 3 PDG 4 QRQLL Time () Fig. 6. Load power under reonance excitation 5 5 Frequency (Hz) Fig. 7 Reonance frequency (Zd=mH)
15 3 The relation preented in Eq. () and Eq. () are preented in Fig. 6, where the total load power i higher than the power upplied by both of the noncontrollable DG and DG. The active power P DG of the controllable DGS i contant and equal to it reference (P DGref =4kW). Fig. 7 preent the pectral repone of the grid ide current in DG that depict the preence of a pike at f=9hz due to the reonance phenomenon appearance. By identification, a grid inductance of L g =.75mH i etimated. Indeed, the propoed hybrid method can be ued to improve the MG output quality after the ilanding detection. In fact, the method allow the etimation of grid impedance that varie under grid fault or grid blackout; hence if the etimated grid impedance value exceed the limit the IBS will open to diconnect the MG. In other way, if it i below the limit ( Z g <Ω), the DGS control trategy hould adopt the grid parameter to maintain the output power quality and to avoid the interaction effect; hence ytem control reconfiguration i needed. In the propoed MG tructure, the virtual reitance i ued not only to damp the ytem (DG and DG) and to drive the ytem near the reonance to extract the grid parameter but alo for ytem reconfiguration reaon. The virtual reitance ha the ability to maintain the ytem pole location and hence maintaining the ytem tability and reliability by returning the ytem pole, changed due to grid impedance variation, to their initial place. 5. Concluion In the next decade, power quality and ervice continuity will be the mot important feature on which the reearch interet relie. For thi reaon, ilanding condition detection i well invetigated in the microgrid power quality improvement, to enure the eamle tranition between the operating mode gridconnected and the ilanded mode, and alo for protection reaon. In thi way, a hybrid ilanding detection method i preented in pecific MG tructure. Thi ilanding method i baed on reonance injection after grid parameter variation detection and it i able to detect the ilanding under wort condition. Indeed, the algorithm i implemented in the cloet DGS of MG to the grid to avoid the interaction between the parallelinverter under reonance tate and it i capable to reconfigure the ytem control trategy by introducing the new grid parameter. During reonance excitation and throughout ilanded mode, controllable DGS i ued to upport the frequency and voltage of MG while the parallel inverter act a current ource. The propoed detection algorithm i a proper and efficient olution for both intentional and unintentional ilanding detection while the propoed MG tructure i well flexible in term of high MG power quality maintaining. Reference [ A. H. K. Alaboudy, H. H. Zeineldin, Ilanding detection for inverterbaed dg coupled with frequencydependent tatic load, IEEE Tran. Power. Deliv. () [ H. Berriri, M.W. Naouar, I. SlamaBelkhodja, Senor fault tolerant control for wind turbine ytem with doubly fed induction generator, ELECTRIMACS, 68th June, CergyPontoie, France,. [3 W. Ghzaiel, M. JebaliBen Ghorbal, I. SlamaBelkhodja, J. M. Guerrero, A novel grid impedance etimation technique baed on adaptive virtual reitance control loop applied to ditributed generation inverter, IEEE conference in Power Electronic and Application (3). [4 J. M. Guerrero, J. Mata, L. G. de Vicuna, M. Catilla, J. Miret, Decentralized control of parallel operation of ditributed generation inverter uing reitive output impedance, IEEE Tran. Ind. Appl. (7) [5 J. M. Guerrero, J. C. Vaquez, J. Mata, M. Catilla, L. G. de Vicuna, Control trategy for flexible microgrid baed on parallel lineinteractive UPS ytem, IEEE Tran. Ind. Electron. (9) [6 J. B. Jeong, H. J. Kim, Active antiilanding method for PV ytem uing reactive power control, IET Electronic Letter (6) 4 5. [7 Y. A. R. I. Mohamed, E. F. ElSaadany, Adaptive decentralized droop controller to preerve power haring tability of paralleled inverter in ditributed generation microgrid, IEEE Tran. Power. Electron. (8) [8 J. Rocabert, Gutavo M. S. Azevedo, A. Luna, J. M. Guerrero, J. I. Candela, P. Rodrıguez, Intelligent connection agent for threephae gridconnected microgrid, IEEE Tran. Power. Electron. () [9 P. Rodríguez, A. Luna, I. Candela, R. Mujal, R.Teodorecu, F. Blaabjerg, Multireonant frequencylocked loop for grid ynchronization of power converter under ditorted grid condition, IEEE Tran. Ind. Electron. ( ) 738.
16 [ P. Rodriguez, A. Luna, R. S. MunozAguilar, I. EtxeberriaOtadui, R. Teodorecu, F. Blaabjerg, A tationary reference frame grid ynchronization ytem for threephae gridconnected power converter under advere grid condition, IEEE Tran. Power. Electron. () [ S. Seman, J. Niiranen, A. Arkkio, Ridethrough analyi of doubly fed induction windpower generator under unymmetrical network diturbance, IEEE Tran. Power. Syt. ( 6) [ A.V. Timbu, P. Rodriguez, R. Teodorecu, M. Ciobotaru, Line impedance etimation uing active and reactive power variation, IEEE Power Electronic Specialit Conference (7) [3 R. Teodorecu, F. Blaabjerg, M. Lierre, P.C. Loh, Proportionalreonant controller and filter for gridconnected voltageource converter, IET Electric Power Application, (6) [4 H. Vahedi, M. Karrari, Adaptive fuzzy andia frequencyhift method for ilanding protection of inverterbaed ditributed generation, IEEE Tran. Power. Deliv, (3) [5 J.C. Vaquez, J.M. Guerrero, A. Luna, P. Rodriguez, R. Teodorecu, Adaptive droop control applied to voltageource inverter operating in gridconnected and ilanded mode, IEEE Tran. Ind. Electron. (9) [6 J. C. Vaquez, J. M. Guerrero, J. Miret, M. Catilla, L. G. Vicuna, Hierarchical control of intelligent Microgrid, IEEE Ind. Electron. Mag. () 39. [7 J. C. Vaquez, J. M. Guerrero, M. Savaghebi, R. Teodorecu, Modeling, analyi, and deign of tationary reference frame droop controlled parallel threephae voltage ource inverter, IEEE Tran. Ind. Electron. (3) 7 8. [8 X. Wang, J. M. Guerrero, Z Chen, Control of grid interactive AC Mmicrogrid, IEEE conference in Indutrial Electronic (ISIE) ()  6 [9 Y. Zhu, D. Xu, N. He, J. Ma, J. Zhang, Y. Zhang,G. Shen, C. Hu, A Novel RPV (ReactivePowerVariation) Antiilanding method baed on adapted reactive power perturbation, IEEE Tran. Power. Electron. (3)
Published in: Proceedings of the 15th European Conference on Power Electronics and Applications, EPE 2013
Aalborg Universitet A Novel Grid Impedance Estimation Technique based on Adaptive Virtual Resistance Control Loop Applied to Distributed Generation Inverters Ghzaiel, Walid; JebaliBen Ghorbal, Manel;
More informationQuestion 1 Equivalent Circuits
MAE 40 inear ircuit Fall 2007 Final Intruction ) Thi exam i open book You may ue whatever written material you chooe, including your cla note and textbook You may ue a hand calculator with no communication
More informationFUNDAMENTALS OF POWER SYSTEMS
1 FUNDAMENTALS OF POWER SYSTEMS 1 Chapter FUNDAMENTALS OF POWER SYSTEMS INTRODUCTION The three baic element of electrical engineering are reitor, inductor and capacitor. The reitor conume ohmic or diipative
More informationR. W. Erickson. Department of Electrical, Computer, and Energy Engineering University of Colorado, Boulder
R. W. Erickon Department of Electrical, Computer, and Energy Engineering Univerity of Colorado, Boulder Cloedloop buck converter example: Section 9.5.4 In ECEN 5797, we ued the CCM mall ignal model to
More informationChapter 9: Controller design. Controller design. Controller design
Chapter 9. Controller Deign 9.. Introduction 9.2. Eect o negative eedback on the network traner unction 9.2.. Feedback reduce the traner unction rom diturbance to the output 9.2.2. Feedback caue the traner
More informationIII.9. THE HYSTERESIS CYCLE OF FERROELECTRIC SUBSTANCES
III.9. THE HYSTERESIS CYCLE OF FERROELECTRIC SBSTANCES. Work purpoe The analyi of the behaviour of a ferroelectric ubtance placed in an eternal electric field; the dependence of the electrical polariation
More informationNonlinear SingleParticle Dynamics in High Energy Accelerators
Nonlinear SingleParticle Dynamic in High Energy Accelerator Part 6: Canonical Perturbation Theory Nonlinear SingleParticle Dynamic in High Energy Accelerator Thi coure conit of eight lecture: 1. Introduction
More informationinto a discrete time function. Recall that the table of Laplace/ztransforms is constructed by (i) selecting to get
Lecture 25 Introduction to Some Matlab c2d Code in Relation to Sampled Sytem here are many way to convert a continuou time function, { h( t) ; t [0, )} into a dicrete time function { h ( k) ; k {0,,, }}
More informationA Parallel Power Conditioning System with Energy Storage Capability for Power Quality Improvement in Industrial Plants
A Parallel Power onditioning Sytem with Energy Storage apability for Power Quality Improvement in Indutrial Plant, Gabriele Grandi, laudio Roi DIPARTIMENTO DI INGEGNERIA ELETTRIA Univerità degli Studi
More informationPublication V by authors
Publication Kontantin S. Kotov and Jorma J. Kyyrä. 008. nertion lo and network parameter in the analyi of power filter. n: Proceeding of the 008 Nordic Workhop on Power and ndutrial Electronic (NORPE 008).
More informationDynamic Simulation of a ThreePhase Induction Motor Using Matlab Simulink
Dynamic Simulation of a ThreePhae Induction Motor Uing Matlab Simulink Adel Aktaibi & Daw Ghanim, graduate tudent member, IEEE, M. A. Rahman, life fellow, IEEE, Faculty of Engineering and Applied Science,
More informationLecture 4 Topic 3: General linear models (GLMs), the fundamentals of the analysis of variance (ANOVA), and completely randomized designs (CRDs)
Lecture 4 Topic 3: General linear model (GLM), the fundamental of the analyi of variance (ANOVA), and completely randomized deign (CRD) The general linear model One population: An obervation i explained
More informationSimple Observer Based Synchronization of Lorenz System with Parametric Uncertainty
IOSR Journal of Electrical and Electronic Engineering (IOSRJEEE) ISSN: 78676Volume, Iue 6 (Nov.  Dec. 0), PP 40 Simple Oberver Baed Synchronization of Lorenz Sytem with Parametric Uncertainty Manih
More informationDesign By Emulation (Indirect Method)
Deign By Emulation (Indirect Method he baic trategy here i, that Given a continuou tranfer function, it i required to find the bet dicrete equivalent uch that the ignal produced by paing an input ignal
More informationECE382/ME482 Spring 2004 Homework 4 Solution November 14,
ECE382/ME482 Spring 2004 Homework 4 Solution November 14, 2005 1 Solution to HW4 AP4.3 Intead of a contant or tep reference input, we are given, in thi problem, a more complicated reference path, r(t)
More informationStudy on the effect of vent on the electroacoustic absorber
INTERNOISE 016 Study on the effect of vent on the electroacoutic aborber Youngeun Cho 1 ; Semyung Wang 1, Gwangju Intitute of Science and Technology, Republic of Korea ABSTRACT Electroacoutic aborber
More information5.5 Application of Frequency Response: Signal Filters
44 Dynamic Sytem Second order lowpa filter having tranfer function H()=H ()H () u H () H () y Firt order lowpa filter Figure 5.5: Contruction of a econd order lowpa filter by combining two firt order
More informationWhat lies between Δx E, which represents the steam valve, and ΔP M, which is the mechanical power into the synchronous machine?
A 2.0 Introduction In the lat et of note, we developed a model of the peed governing mechanim, which i given below: xˆ K ( Pˆ ˆ) E () In thee note, we want to extend thi model o that it relate the actual
More informationEE Control Systems LECTURE 14
Updated: Tueday, March 3, 999 EE 434  Control Sytem LECTURE 4 Copyright FL Lewi 999 All right reerved ROOT LOCUS DESIGN TECHNIQUE Suppoe the cloedloop tranfer function depend on a deign parameter k We
More informationA PLC BASED MIMO PID CONTROLLER FOR MULTIVARIABLE INDUSTRIAL PROCESSES
ABCM Sympoium Serie in Mechatronic  Vol. 3  pp.8796 Copyright c 8 by ABCM A PLC BASE MIMO PI CONOLLE FO MULIVAIABLE INUSIAL POCESSES Joé Maria Galvez, jmgalvez@ufmg.br epartment of Mechanical Engineering
More informationAssessment of Performance for Single Loop Control Systems
Aement of Performance for Single Loop Control Sytem HiaoPing Huang and JyhCheng Jeng Department of Chemical Engineering National Taiwan Univerity Taipei 1617, Taiwan Abtract Aement of performance in
More informationBehavioral Modeling of Transmission Line Channels via Linear Transformations
Behavioral Modeling of Tranmiion Line Channel via Linear Tranformation Albert Vareljian albertv@ieeeorg Member, IEEE, Canada Abtract An approach baed on the linear tranformation of network port variable
More informationClustering Methods without Given Number of Clusters
Clutering Method without Given Number of Cluter Peng Xu, Fei Liu Introduction A we now, mean method i a very effective algorithm of clutering. It mot powerful feature i the calability and implicity. However,
More informationCONTROL SYSTEMS, ROBOTICS AND AUTOMATION Vol. VIII Decoupling Control  M. Fikar
DECOUPLING CONTROL M. Fikar Department of Proce Control, Faculty of Chemical and Food Technology, Slovak Univerity of Technology in Bratilava, Radlinkého 9, SK812 37 Bratilava, Slovakia Keyword: Decoupling:
More informationRepresentation of a Group of Threephase Induction Motors Using Per Unit Aggregation Model A.Kunakorn and T.Banyatnopparat
epreentation of a Group of Threephae Induction Motor Uing Per Unit Aggregation Model A.Kunakorn and T.Banyatnopparat AbtractThi paper preent a per unit gregation model for repreenting a group of threephae
More informationDYNAMIC MODELS FOR CONTROLLER DESIGN
DYNAMIC MODELS FOR CONTROLLER DESIGN M.T. Tham (996,999) Dept. of Chemical and Proce Engineering Newcatle upon Tyne, NE 7RU, UK.. INTRODUCTION The problem of deigning a good control ytem i baically that
More informationNONLINEAR CONTROLLER DESIGN FOR A SHELL AND TUBE HEAT EXCHANGER AN EXPERIMENTATION APPROACH
International Journal of Electrical, Electronic and Data Communication, ISSN: 232284 Volume3, Iue8, Aug.25 NONLINEAR CONTROLLER DESIGN FOR A SHELL AND TUBE HEAT EXCHANGER AN EXPERIMENTATION APPROACH
More informationPublished in: Proceedings of the 16th IEEE Mediterranean Electrotechnical Conference (MELECON), 2012
Aalborg Universitet Online Detection and Estimation of Grid Impedance Variation for Distributed Power Generation JebaliBen Ghorbal, Manel; Ghzaiel, Walid; SlamaBelkhodja, Ilhem; Guerrero, Josep M. Published
More informationAPPLICATION OF THE SINGLE IMPACT MICROINDENTATION FOR NON DESTRUCTIVE TESTING OF THE FRACTURE TOUGHNESS OF NONMETALLIC AND POLYMERIC MATERIALS
APPLICATION OF THE SINGLE IMPACT MICROINDENTATION FOR NON DESTRUCTIVE TESTING OF THE FRACTURE TOUGHNESS OF NONMETALLIC AND POLYMERIC MATERIALS REN A. P. INSTITUTE OF APPLIED PHYSICS OF THE NATIONAL ACADEMY
More informationCodes Correcting Two Deletions
1 Code Correcting Two Deletion Ryan Gabry and Frederic Sala Spawar Sytem Center Univerity of California, Lo Angele ryan.gabry@navy.mil fredala@ucla.edu Abtract In thi work, we invetigate the problem of
More informationComparing Means: ttests for Two Independent Samples
Comparing ean: ttet for Two Independent Sample Independenteaure Deign ttet for Two Independent Sample Allow reearcher to evaluate the mean difference between two population uing data from two eparate
More informationA NEW LOAD MODEL OF THE PEDESTRIANS LATERAL ACTION
A NEW LOAD MODEL OF THE PEDESTRIANS LATERAL ACTION Fiammetta VENUTI PhD Politecnico di Torino Torino, IT Luca Bruno Aociate Profeor Politecnico di Torino Torino, IT Summary Thi paper propoe a new load
More informationNoload And Blocked Rotor Test On An Induction Machine
Noload And Blocked Rotor Tet On An Induction Machine Aim To etimate magnetization and leakage impedance parameter of induction machine uing noload and blocked rotor tet Theory An induction machine in
More informationECE 325 Electric Energy System Components 6 ThreePhase Induction Motors. Instructor: Kai Sun Fall 2015
ECE 35 Electric Energy Sytem Component 6 ThreePhae Induction Motor Intructor: Kai Sun Fall 015 1 Content (Material are from Chapter 1315) Component and baic principle Selection and application Equivalent
More informationRealTime Identification of Sliding Friction Using LabVIEW FPGA
RealTime Identification of Sliding Friction Uing LabVIEW FPGA M. Laine Mear, Jeannie S. Falcon, IEEE, and Thoma R. Kurfe, IEEE Abtract Friction i preent in all mechanical ytem, and can greatly affect
More informationRoot Locus Diagram. Root loci: The portion of root locus when k assume positive values: that is 0
Objective Root Locu Diagram Upon completion of thi chapter you will be able to: Plot the Root Locu for a given Tranfer Function by varying gain of the ytem, Analye the tability of the ytem from the root
More informationDirect Torque Control of Saturated Induction Machine with and without speed sensor
Journal of Advanced Reearch in Science and Technology ISSN: 23529989 Direct Torque Control of Saturated Induction Machine with and without peed enor Tahar Djellouli,2, Samir Moulahoum, Med Seghir Boucherit
More informationEfficient Global Optimization Applied to MultiObjective Design Optimization of Lift Creating Cylinder Using Plasma Actuators
Efficient Global Optimization Applied to MultiObjective Deign Optimization of Lift Creating Cylinder Uing Plama Actuator Maahiro Kanazaki 1, Takahi Matuno 2, Kengo Maeda 2 and Mituhiro Kawazoe 2 1 Graduate
More informationUse of Modal Sensitivity to Operating Conditions for Damping Control in Power Systems
Proceeding of the 44th Hawaii International Conference on Sytem Science  Ue of Modal Senitivity to Operating Condition for Damping Control in Power Sytem Zhenyu Huang ing Zhou Franci Tuffner Daniel Trudnowki
More informationDynamic Simulation of NEK Reactor Coolant Pump with a Best Estimate Full Scale Model in APROS
Dynamic Simulation of NEK Reactor Coolant Pump with a Bet Etimate Full Scale Model in APROS ABSTRACT Dejan Slovenc ZELEN d.o.o. Hočevarjev trg 1, 870, Krško, Slovenia dejan.lovenc@zelen.i Ivica Bašić
More informationLecture 8  SISO Loop Design
Lecture 8  SISO Loop Deign Deign approache, given pec Loophaping: inband and outofband pec Fundamental deign limitation for the loop Gorinevky Control Engineering 81 Modern Control Theory Appy reult
More informationTrellis Shaping Techniques for Satellite Telecommunication Systems
> 1 Trelli Technique for Satellite Telecommunication Sytem M. ÁlvarezDíaz 1, M. Neri, C. Moquera 1 and G. E. Corazza 1 Dept. Signal Theory and Communication (TSC), Univerity of Vigo Campu Univeritario
More informationProperties of Ztransform Transform 1 Linearity a
Midterm 3 (Fall 6 of EEG:. Thi midterm conit of eight ingleided page. The firt three page contain variou table followed by FOUR eam quetion and one etra workheet. You can tear out any page but make ure
More informationEmittance limitations due to collective effects for the TOTEM beams
LHC Project ote 45 June 0, 004 Elia.Metral@cern.ch Andre.Verdier@cern.ch Emittance limitation due to collective effect for the TOTEM beam E. Métral and A. Verdier, ABABP, CER Keyword: TOTEM, collective
More informationModule 4: Time Response of discrete time systems Lecture Note 1
Digital Control Module 4 Lecture Module 4: ime Repone of dicrete time ytem Lecture Note ime Repone of dicrete time ytem Abolute tability i a baic requirement of all control ytem. Apart from that, good
More informationMATHEMATICAL MODELING OF INDUCTION MOTORS
37 CHAPTER 3 MATHEMATICAL MODELING OF INDUCTION MOTORS To tart with, a wellknown technique called the SVPWM technique i dicued a thi form the bai of the mathematical modeling of IM. Furthermore, the d
More informationImproving the Efficiency of a Digital Filtering Scheme for Diabatic Initialization
1976 MONTHLY WEATHER REVIEW VOLUME 15 Improving the Efficiency of a Digital Filtering Scheme for Diabatic Initialization PETER LYNCH Met Éireann, Dublin, Ireland DOMINIQUE GIARD CNRM/GMAP, MétéoFrance,
More informationChapter 13. Root Locus Introduction
Chapter 13 Root Locu 13.1 Introduction In the previou chapter we had a glimpe of controller deign iue through ome imple example. Obviouly when we have higher order ytem, uch imple deign technique will
More informationOn Stability of Electronic Circuits
roceeding of the th WSAS International Conference on CIUITS On Stability of lectronic Circuit HASSAN FATHABADI lectrical ngineering Department Azad Univerity (South Tehran Branch) Tehran, IAN h4477@hotmailcom
More informationState Space: Observer Design Lecture 11
State Space: Oberver Deign Lecture Advanced Control Sytem Dr Eyad Radwan Dr Eyad Radwan/ACS/ State SpaceL Controller deign relie upon acce to the tate variable for feedback through adjutable gain. Thi
More informationOptimization model in Input output analysis and computable general. equilibrium by using multiple criteria nonlinear programming.
Optimization model in Input output analyi and computable general equilibrium by uing multiple criteria nonlinear programming Jing He * Intitute of ytem cience, cademy of Mathematic and ytem cience Chinee
More informationAn Improved Flux Observer for Sensorless Permanent Magnet Synchronous Motor Drives with Parameter Identification
J Electr Eng Technol Vol. 8, No. 3: 51653, 13 http://dx.doi.org/1.537/jeet.13.8.3.516 ISSN(Print) 19751 ISSN(Online) 93743 An Improved Flux Oberver for Senorle Permanent Magnet Synchronou Motor Drive
More informationSolving Differential Equations by the Laplace Transform and by Numerical Methods
36CH_PHCalter_TechMath_95099 3//007 :8 PM Page Solving Differential Equation by the Laplace Tranform and by Numerical Method OBJECTIVES When you have completed thi chapter, you hould be able to: Find the
More informationLateral vibration of footbridges under crowdloading: Continuous crowd modeling approach
ateral vibration of footbridge under crowdloading: Continuou crowd modeling approach Joanna Bodgi, a, Silvano Erlicher,b and Pierre Argoul,c Intitut NAVIER, ENPC, 6 et 8 av. B. Pacal, Cité Decarte, Champ
More information4.6 Principal trajectories in terms of amplitude and phase function
4.6 Principal trajectorie in term of amplitude and phae function We denote with C() and S() the coinelike and inelike trajectorie relative to the tart point = : C( ) = S( ) = C( ) = S( ) = Both can be
More informationSeveral schematic symbols for a capacitor are shown below. The symbol resembles the two conducting surfaces separated with a dielectric.
Capacitor Capacitor are two terminal, paive energy torage device. They tore electrical potential energy in the form of an electric field or charge between two conducting urface eparated by an inulator
More informationAn Approach to Design MIMO FO Controllers for Unstable Nonlinear Plants
338 IEEE/CAA JOURAL OF AUTOMATICA SIICA VOL. 3 O. 3 JULY 26 An Approach to Deign MIMO FO Controller for Untable onlinear Plant Arturo RojaMoreno Senior Member IEEE Abtract Thi paper develop an approach
More informationCHARGING OF DUST IN A NEGATIVE ION PLASMA (APS DPP06 Poster LP )
1 CHARGING OF DUST IN A NEGATIVE ION PLASMA (APS DPP06 Poter LP1.00128) Robert Merlino, Ro Fiher, Su Hyun Kim And Nathan Quarderer Department of Phyic and Atronomy, The Univerity of Iowa Abtract. We invetigate
More informationThe stabilization interval system of a tethered descent underwater vehicle
IOP Conference Serie: Material Science and Engineering PAPER OPEN ACCESS The tabilization interval ytem of a tethered decent underwater vehicle To cite thi article: S A Gayvoronkiy et al 016 IOP Conf.
More informationIEEE TRANSACTIONS ON VEHICULAR TECHNOLOGY, VOL. 65, NO. 10, OCTOBER Wenguang Mao, Xudong Wang, Senior Member, IEEE, and Shanshan Wu
IEEE TRANSACTIONS ON VEHICULAR TECHNOLOGY, VOL. 65, NO. 10, OCTOBER 2016 8511 Ditributed Opportunitic Scheduling With QoS Contraint for Wirele Network With Hybrid Link Wenguang Mao, Xudong Wang, Senior
More informationStability regions in controller parameter space of DC motor speed control system with communication delays
Stability region in controller parameter pace of DC motor peed control ytem with communication delay Şahin Sönmez, Saffet Ayaun Department of Electrical and Electronic Engineering, Nigde Univerity, 5124,
More informationEFFECT ON PERSISTENCE OF INTRASPECIFIC COMPETITION IN COMPETITION MODELS
Electronic Journal of Differential Equation, Vol. 2007(2007, No. 25, pp. 0. ISSN: 072669. URL: http://ejde.math.txtate.edu or http://ejde.math.unt.edu ftp ejde.math.txtate.edu (login: ftp EFFECT ON PERSISTENCE
More informationA Compensated Acoustic Actuator for Systems with Strong Dynamic Pressure Coupling
A Compenated Acoutic Actuator for Sytem with Strong Dynamic Preure Coupling Submitted to ASME Journal of Vibration and Acoutic July.997 Charle Birdong and Clark J. Radcliffe Department of Mechanical Engineering
More informationPulsed Magnet Crimping
Puled Magnet Crimping Fred Niell 4/5/00 1 Magnetic Crimping Magnetoforming i a metal fabrication technique that ha been in ue for everal decade. A large capacitor bank i ued to tore energy that i ued to
More informationTHE IDENTIFICATION OF THE OPERATING REGIMES OF THE CONTROLLERS BY THE HELP OF THE PHASE TRAJECTORY
Mariu M. B LA Aurel Vlaicu Univerity of Arad, Engineering Faculty Bd. Revolu iei nr. 77, 3030, Arad, Romania, Email: mariu.bala@ieee.org THE IDENTIFICATION OF THE OPERATING REGIMES OF THE CONTROLLERS
More informationA Bluffer s Guide to... Sphericity
A Bluffer Guide to Sphericity Andy Field Univerity of Suex The ue of repeated meaure, where the ame ubject are teted under a number of condition, ha numerou practical and tatitical benefit. For one thing
More informationOnline Appendix for Managerial Attention and Worker Performance by Marina Halac and Andrea Prat
Online Appendix for Managerial Attention and Worker Performance by Marina Halac and Andrea Prat Thi Online Appendix contain the proof of our reult for the undicounted limit dicued in Section 2 of the paper,
More informationAn Experimental Examination of a Fuzzy Logic Based DTC Scheme
011 nd Power Electronic, Drive Sytem and echnologie Conference An Experimental Examination of a Fuzzy Logic Baed DC Scheme H. Valizadeh Haghi, B. Ekandari, E. Pahajavid, M. avakoli Bina Dept. of Electrical
More informationSeismic Loads Based on IBC 2015/ASCE 710
Seimic Load Baed on IBC 2015/ASCE 710 Baed on Section 1613.1 of IBC 2015, Every tructure, and portion thereof, including nontructural component that are permanently attached to tructure and their upport
More informationTHE RATIO OF DISPLACEMENT AMPLIFICATION FACTOR TO FORCE REDUCTION FACTOR
3 th World Conference on Earthquake Engineering Vancouver, B.C., Canada Augut 6, 4 Paper No. 97 THE RATIO OF DISPLACEMENT AMPLIFICATION FACTOR TO FORCE REDUCTION FACTOR Mua MAHMOUDI SUMMARY For Seimic
More informationEE Control Systems LECTURE 6
Copyright FL Lewi 999 All right reerved EE  Control Sytem LECTURE 6 Updated: Sunday, February, 999 BLOCK DIAGRAM AND MASON'S FORMULA A linear timeinvariant (LTI) ytem can be repreented in many way, including:
More informationA NEW EQUIVALENT CIRCUIT OF THE THREEPHASE INDUCTION MOTOR (CASE STUDIES:CURRENT AND POWER FACTOR OF THE MOTOR)
VO. 1, NO. 3, DECEBER 017 SSN 18196608 ARPN Journal of Engineering and Applied Science 006017 Aian Reearch Publihing Network (ARPN. All right reerved. www.arpnjournal.com A NEW EQUVAENT CRCUT OF THE
More informationEE C128 / ME C134 Problem Set 1 Solution (Fall 2010) Wenjie Chen and Jansen Sheng, UC Berkeley
EE C28 / ME C34 Problem Set Solution (Fall 200) Wenjie Chen and Janen Sheng, UC Berkeley. (0 pt) BIBO tability The ytem h(t) = co(t)u(t) i not BIBO table. What i the region of convergence for H()? A bounded
More informationModeling and Simulation of a TwoMass Resonant System with Speed Controller
International ournal of Information and Electronic Engineering, Vol. 3, No. 5, eptember 203 odeling and imulation of a Twoa Reonant ytem with peed ontroller Ghazanfar hahgholian, ember, IAIT Abtract The
More informationEstimation of Temperature Rise in Stator Winding and Rotor Magnet of PMSM Based on EKF
2010 3rd International Conference on Computer and Electrical Engineering (ICCEE 2010) IPCSIT vol. 53 (2012) (2012) IACSIT Pre, Singapore DOI: 10.7763/IPCSIT.2012.V53.No.2.37 Etimation of Temperature Rie
More informationInput Impedance and Transfer Function of NStage CockcroftWalton Voltage Multiplier
Input Impedance and Tranfer Function of NStae ockcroftwalton Voltae ltiplier Xavier Le Polozec Abtract Thi paper provide theoretical prediction of the differential input impedance, tranfer function,
More informationOn the Stability Region of Congestion Control
On the Stability Region of Congetion Control Xiaojun Lin and Ne B. Shroff School of Electrical and Computer Engineering Purdue Univerity, Wet Lafayette, IN 47906 {linx,hroff}@ecn.purdue.edu Abtract It
More informationAalborg Universitet. Publication date: Document Version Publisher's PDF, also known as Version of record
Aalborg Univeritet Modelbaed Control of a Bottom Fired Marine Boiler Solberg, Brian Willum; Kartenen, Clau M. S.; Anderen, Palle; Pederen, Tom Søndergård; Hvitendahl, Poul U. Publication date: 2005 Document
More informationPreemptive scheduling on a small number of hierarchical machines
Available online at www.ciencedirect.com Information and Computation 06 (008) 60 619 www.elevier.com/locate/ic Preemptive cheduling on a mall number of hierarchical machine György Dóa a, Leah Eptein b,
More informationObserving Condensations in Atomic Fermi Gases
Oberving Condenation in Atomic Fermi Gae (Term Eay for 498ESM, Spring 2004) Ruqing Xu Department of Phyic, UIUC (May 6, 2004) Abtract Oberving condenation in a ga of fermion ha been another intereting
More informationRobustness analysis for the boundary control of the string equation
Routne analyi for the oundary control of the tring equation Martin GUGAT Mario SIGALOTTI and Mariu TUCSNAK I INTRODUCTION AND MAIN RESULTS In thi paper we conider the infinite dimenional ytem determined
More informationFOURIERBASED METHODS FOR THE SPECTRAL ANALYSIS OF MUSICAL SOUNDS. Sylvain Marchand
FOUIEBAS METHOS FO THE SPECTAL ANALYSIS OF MUSICAL SOUNS Sylvain Marchand Univerity of Bret, LabSTICC CNS UM 628, 292 Bret, Brittany, France ABSTACT When dealing with muical ound, the horttime Fourier
More informationSpring 2014 EE 445S RealTime Digital Signal Processing Laboratory. Homework #0 Solutions on Review of Signals and Systems Material
Spring 4 EE 445S RealTime Digital Signal Proceing Laboratory Prof. Evan Homework # Solution on Review of Signal and Sytem Material Problem.. ContinuouTime Sinuoidal Generation. In practice, we cannot
More informationFeedback Control Systems (FCS)
Feedback Control Sytem (FCS) Lecture1920 RouthHerwitz Stability Criterion Dr. Imtiaz Huain email: imtiaz.huain@faculty.muet.edu.pk URL :http://imtiazhuainkalwar.weebly.com/ Stability of Higher Order
More information5. NONLINER BLOCKS Nonlinear standard blocks
5. NONLINER BLOCKS In previou chapter continuou tem or tem where to the change of the input a change of the output correponded, which in the whole range of the ignal value could be expreed b one equation,
More informationAn Imageencoded MachZehnder Joint Transform Correlator for Polychromatic Pattern Recognition with Multilevel Quantized Reference Functions
Proceeding of the International MultiConference of Engineer and Computer Scientit 008 Vol I IMECS 008, 191 March, 008, Hong Kong An Imageencoded MachZehnder Joint Tranform Correlator for Polychromatic
More informationSpatialModeShape Identification using a Continuous Wavelet Transform
Strojniški vetnik  Journal of Mechanical Engineering 55(009)5, StartPageEndPage Paper received: 09.0.009 UDC 53/533 Paper accepted: 00.00.00x SpatialModeShape Identification uing a Continuou Wavelet
More informationBasics of a Quartz Crystal Microbalance
Baic of a Quartz Crytal Microbalance Introduction Thi document provide an introduction to the quartz crytal microbalance (QCM) which i an intrument that allow a uer to monitor mall ma change on an electrode.
More informationPerformance Evaluation
Performance Evaluation 95 (206) 40 Content lit available at ScienceDirect Performance Evaluation journal homepage: www.elevier.com/locate/peva Optimal cheduling in call center with a callback option Benjamin
More informationSynchronous Machines  Structure
Synchronou Machine  Structure Synchronou Machine  Structure rotate at contant peed. primary energy converion device of the word electric power ytem. both generator and motor operation can draw either
More informationMODERN CONTROL SYSTEMS
MODERN CONTROL SYSTEMS Lecture 1 Root Locu Emam Fathy Department of Electrical and Control Engineering email: emfmz@aat.edu http://www.aat.edu/cv.php?dip_unit=346&er=68525 1 Introduction What i root locu?
More information84 ZHANG JingShang Vol. 39 of which would emit 5 He rather than 3 He. 5 He i untable and eparated into n + pontaneouly, which can alo be treated a if
Commun. Theor. Phy. (Beijing, China) 39 (003) pp. 83{88 c International Academic Publiher Vol. 39, No. 1, January 15, 003 Theoretical Analyi of Neutron DoubleDierential Cro Section of n+ 11 B at 14. MeV
More informationAt the end of this lesson, the students should be able to understand:
Intructional Objective: At the end of thi leon, the tudent hould be able to undertand: Baic failure mechanim of riveted joint. Concept of deign of a riveted joint. 1. Strength of riveted joint: Strength
More informationComputers and Mathematics with Applications. Sharp algebraic periodicity conditions for linear higher order
Computer and Mathematic with Application 64 (2012) 2262 2274 Content lit available at SciVere ScienceDirect Computer and Mathematic with Application journal homepage: wwweleviercom/locate/camwa Sharp algebraic
More informationHOMEWORK ASSIGNMENT #2
Texa A&M Univerity Electrical Engineering Department ELEN Integrated Active Filter Deign Methodologie Alberto ValdeGarcia TAMU ID# 000 17 September 0, 001 HOMEWORK ASSIGNMENT # PROBLEM 1 Obtain at leat
More informationModelling and WaveletBased Identification of 3DOF Vehicle Suspension System
Journal of Software Engineering and Application, 011, 4, 67681 doi:10.436/jea.011.41079 Publihed Online December 011 (http://www.scirp.org/journal/jea) Modelling and WaveletBaed Identification of 3DOF
More informationKukkola, Jarno & Hinkkanen, Marko State observer for gridvoltage sensorless control of a gridconnected converter equipped with an LCL filter
Powered by TCPDF (www.tcpdf.org) Thi i an electronic reprint of the original article. Thi reprint may differ from the original in pagination and typographic detail. Author(): Title: Kukkola, Jarno & Hinkkanen,
More informationIndustrial Temperature PID Controller for PbFree Soldering Iron?
Proceeding of the 17th World Congre The International Federation of Automatic Control Indutrial Temperature PID Controller for PbFree Soldering Iron? Hiroto Hamane Kazuki Hirano Koichi Kae Kazuyohi Miyazaki
More informationListenandTalk: Fullduplex Cognitive Radio Networks
LitenandTalk: Fullduplex Cognitive Radio Network Yun Liao, Tianyu Wang, Lingyang Song, and Zhu Han State Key Laboratory of Advanced Optical Communication Sytem and Network, School of Electrical Engineering
More informationOptimizing Costsensitive Trustnegotiation Protocols
Optimizing Cotenitive Trutnegotiation Protocol Weifeng Chen, Lori Clarke, Jim Kuroe, Don Towley Department of Computer Science Univerity of Maachuett, Amhert {chenwf, clarke, kuroe, towley}@c.uma.edu
More information